Furnace heater heat maintenance
American stand system tune up. Filter was clean
1 system tune up + replaced 18x20x1 filter.
1 system tune up + replaced 16x25x1 filter. Recommendation blower wheel clean, add 5x4x3 y
Replaced Amana 5" media filter
Replaced in warranty blower motor on a Rheem air handler heat pump system
Fall tune-up on an American Standard system
Installed new thermostat Honeywell 6000 on a Lennox air conditioning gas furnace system
Installed 4 ton American standard full system
Winter furnace tune up on customers to Lennox Systems. Customer provided the filters.
Service Agreement furnace tune ups on customers 2 systems.
Todd and Alec preformed leak search on m/l and u/s system found leak on m/l line set fixed and replaced filter dryer add 15 lbs of 410-a to system. Units are working great in Suwanee ga.
Completed a 3 system heat tune up on older model Trane and an American Standard.