Cleaned furnace drain trap Adjusted slope on furnace drain Adjusted slope on furnace vent Camera inspection of primary and secondary heat exchangers Performed Flu analysis to ensure furnace working properly
Generalaire Model 3200DMM Bypass Humidifier w/ Water Savor Module
Maintenance: Thermostat working Checked gas pressure: 1.9" w.c. low 3.46" w.c. high Cleaned flame sensor Checked operations of safeties Checked furnace filter Checked operation of humidifier Performed flue analysis: furnace operating efficiently
Estimate on water heater , AC and Furnace.
Service Call to repair furnace
Service call to repair a Carrier air conditioner