Tech went right to the problem. Replaced capacitor and cooled down the compressor. Seems to be cooling fine now.
System was low on 410A Took 2 lbs to get charged to proper level. Customer wants to wait to get estimate on new system. Would like quote at another time just not sure when yet.
AC SERVICE REPAIR ON A 2 TON CARRIER HEAT PUMP SYSTEM. REPAIRED LOW VOLTAGE SHORT.
AC SERVICE ON A 3 TON GOODMAN HEAT PUMP PACKAGE UNIT. CHECKED ALL ELECTRICAL CONNECTIONS.
AC SERVICE REPAIR ON A 3 TON CARRIER HEAT PUMP SYSTEM. REPLACED CAPACITOR.
AC SERVICE REPAIR ON A 3 TON CARRIER HEAT PUMP SYSTEM. ORDERED BLOWER MOTOR AND MODULE.
Did tune-up carrier system
AC SERVICE REPAIR ON A 3 TON LENNOX STRAIGHT COOL SYSTEM. ADJUSTED REFRIGERANT CHARGE UNTIL EVAPORATOR COIL CAN BE REPLACED.
AC SERVICE REPAIR ON A 3 TON PAYNE HEAT PUMP SYSTEM. CLEARED CONDENSATION DRAIN LINE.
JetBlue install install fruit that is really great job installing carrier performance heat pump air conditioning system in Spring Hill
After hour repair on a Goodman condenser unit replaced condenser fan motor in Hudson
Carrier system maintenance
AC REPAIR IN HUDSON FL.
Another tune up in hudson on Rheem package system
Recharged split system
Performing annual maintenance