I replaced three wire safety pilot for Bryant boiler. Installed new pilot tubing and fittings. Safety switch closed after 53 seconds of lighting. Boiler operated for about 15 minutes and new pilot assembly failed!! Had new pilot assembly picked up delivered. Replaced again and tested operation. Safety switched closed after 20 seconds. Cycled pilot on and off. Working OK.