Complete 2 system inspection. Find both Airhandler in attic and 2 heatpump system outside. Find 2 21 year old Goodman system. Find both system return plenum rusted and dirty. Find both Airhandler system in attic have no water protection, drain line not run properly and drain pan rusted from water damage. Find Airhandler dirty and blower motor worn, weak blower capacitor. Find both coil rusted but upstairs evaporator freezing up and leaking R22. Duct system poor and not up to code. Find both heatpump unit have replacement fan motor but wire exposed. Find both contactor worn and pitted. Find downstairs heatpump unit have damaged coil. Find fan motor capacitor not mounted. Line insulation missing in different area. Upstairs heatpump low on charge. Insulation in attic also low and need more insulation.