Tech arrived on site. Condenser had power but was not operational. Unit was trying to turn on. Capacitor had been replaced in February by another company. Checked the capacitor and it had failed. Replaced it for testing and found the unit drawing High amperage. And it was drawing LRA. fan motor was under amping but still high. Charge is okay at this time. The capacitor failed because the motor are going out soon. Recommend budgeting for replacement soon. Did the temporary repair to get the unit cooling for the summer. Customer signed up with service agreement.