Replaced very dirty filter. Measured temp splits and refrigerant pressures. Adjusted refrigerant charge by 7 ounces to achieve a higher sub cooling value. Inspected ducting and checked the txv mounted bulb. Tightened down txv compression liquid line connection just as a precaution. I did not notice any odd squeaky sounds at the outdoor unit.