Performed diagnostic on unit. Homeowner states system is not heating. Cycled system for heating, unit kicks on and is cooling. Checked indoor and outdoor connections. Found that reversing valve is energizing in both heating and cooling due to a shorted out wire. Went over findings and recommendations. Homeowner will be running new wire. No other work performed .