Summer AC Maintenance. Upon arrival system is working and operational. I began my maintenance at the outdoor condenser, took apart condenser and cleaned coil with water and our coil solution, removing dirt and debris, system was heavily impacted. Inspected electrical components for wear, tested electricals for amp draw. Checked and measured systems refrigerant pressures and charge. Cleaned service panel. I then proceeded to the indoor furnace unit. Checked electricals ensuring tight connections. Inspected blower wheel compartments for balance and dust build up. Measured temp split, checked main condensate line and safety. Inspected ducts for leakage. Inspector failed due to possible in adequate placement of safety switch, a safety T switch was installed on secondary condensate to ensure passing of inspection. Member mentioned they have allergies, recommended phenomenal aire to help keep home clean and healthy. Upon departure system is working and operational.