AC MAINTENANCE. Found system operational upon arrival. Replaced hepa filter with customer approval. Blower is clean. Evaporator is clean. Duct is in good condition. Washed condenser coil. Freon levels ok. Temp split ok. Compressor amp draw is good at start and run. Condenser motor amps are good. Bearings are ok. Motor control ok and within range. High voltage transfer relay in good condition. Unit operational upon departure.