Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Performed Precision Air Conditioning Tune Up on System. Checked 14x30x1 Air Filter. Filter is starting to get dirty. It is not blocking Air Flow but should be replaced to prevent any issues. Homeowners are going to replace filter. Inspected Electrical Components on Indoor and Outdoor Units. Cleared Condensation Drain Pipe. Tested Auxiliary Pan Float Switch which shuts off the Outdoor Unit. Recommend installing an EZ Trap onto the Drain Line. The EZ Trap gets wired into the system to break R Terminal. If the Trap becomes clogged it will trip the Float Switch and shut the unit down to prevent the drain line from backing up and overflowing. Measured Refrigerant Charge on system. The Disconnect on the Outdoor Unit is broken at the Top Wall Clamp. There is also a crack along the top of the Disconnect Box. Would recommend replacement of the Disconnect Box and whip to prevent any issues. If water gets into the Disconnect Box it could cause electrical issues. System is operating to standards a