Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Performed Six Month Inspection on Amana Gas Furnace system. Replaced 14x24x1 Air Filter. Inspected electrical components. Checked setting programming on system. Put system in Heating Mode and performed Combustion Analysis and measured Gas Pressures. Tested system in Low Stage Heat and High Stage Heat. Tested Humidifier and humidifier was not turning on. Checked Wiring and tested for 24 Volts. The Humidistat Control does not seem to be operating properly. Would recommend removal of the existing Humidistat and installing a new Manual Humidifier Control and rewiring into system. Included an estimate for the Humidifier Control Replacement. The office will call to schedule repair.