Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Found capacitor blown and contactor pitted and burnt, recommended replacement . Replaced 45/7.5 capacitor and 40 amp contactor. Checked 410a refrigerant pressures at 74 degrees. Pressures were 297/131 with 13 degrees subcooling. Checked temperature split at indoor unit. Temperature split was 21 degrees. System is working fine at time of service. Model and serial numbers for outdoor a/c are worn off and sunfaded.