Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Service tech was very pleasant and professional always kind and informative
Performed heating maintenance, checked air filter ok. Cleaned burners and flame sensor, inspected heat exchanger, see rust at seams. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started gas furnace, tested limit and safety switches, measured fuel pressures. Performed combustion test and checked temperature rise.
Performed Six Month Heating Inspection on Amana Gas Furnace. Replaced 20x25x1 Air Filter. Reviewed Cool Cloud Settings and performed System Update On Control Board. Performed Combustion Analysis on Furnace and measured Low Stage and High Stage Gas Pressures. System is operating to standards.
Arrived on job and located equipment to be removed. Removed old gas furnace and coil as well as condenser. Removed old lineset and electrical connections. Set and leveled new pad. Ran new lineset and low volt wires. Ran new thermostat wire. Installed new gas furnace. Bent lineset into outdoor unit and indoor coil, installed txv and brazed with nitrogen. Pressure tested to 275 and bubble tested. No leaks found. Vacuumed down to 300 microns. Weighed in 7 oz of 410a. Connected ductwork and taped seams. Ran condensate, vinyl into discharge line, installed ez trap, and wired pump. Reconnected vent pipe. Wired switch and constant power plug. Ran gas lines and leak checked, no leaks found. Tested operation of condensate pump and furnace/ac. All tests satisfactory at time of install.