Tyler was very helpful polite and did a wonderful job he explained to me what the issue was I would recommend folks to everyone great service
Once again wow service! Noah was super friendly and very informative!
No Heat found burner locked out (Beckett burner). Reset and unit came on and began running normally. Bled oil line to make sure no air was in line, also replaced filters as exsisting filter was dirty. Took temperature rise after replacing filters and temperature stayed with in manufacturers range. System running normally. We will be back the 2nd for cleaning.
Arrives and the customer stated the thermostat display was acting up. The customer said he only had 12v to r and c at the thermostat. Found the ewc board flashing the green lights with 24v of power and I had 24v to the thermostat. Replaced the ewc board and the thermostat. Tested the system and found the blower motor running for 2-4 seconds then turning off and not coming back on. Went over the issue with tech support and found that the blower motor was bad. There must have been a short that started at the ewc board to short multiple components at once. Need to get the customer pricing and availability on the blower motor.
Cleaned and serviced oil boiler. Brushed and vacuumed heat exchanger. Inspected expansion tank, air vents, 3 zone valves, water feeder, circulater pump, and relief valve. Replaced oil filter, pump strainer, and burner nozzle. Performed combustion and efficiency test. Tested 2 heating zones and indirect water heater zone. System operational.
Found something chewed through wire for comprescapacitor. Repaired wind checked operation. System is 20+ years old and in very poor condition. Recommended replacement. No guarantees on system operation.
Arrived and the customer had water all over her basement. The previous tech cleared the drain on the system but did not cap the clean out. This causes water to sit in the pan and over fill. Capped the drain and tested it. The customer would like to speak to management since there is now mold in her basement.
No one answered door. Knocked on door for about 12 minutes called phone number multiple times. Left voicemail.
Ac tune up, cleared trap and drain, tested blower motor and capacitor, replaced filter, inspected coil. Pressures and temperatures, tested all put door components. R22 unit went over phase out with homeowner. Pressures were good and temperatures were good. System running normally.
Found drain line for 1st floor main drain pan forming a vacuum which was not letting the system drain properly, adjusted, checked for cracks on drain pan also filled drain pan with water found no leaks, added new air filter due to the other one being soaked, system operational.
Arrived and the customer stated earlier the system was frozen. It has been off and thawed out. She washed the filters and tried it again but the same thing happened. The system has a history of a refrigerant leak. Gave the customer options to search for the leak and either replace the coil that is leaking or repair it. Also gave pricing g for a replacement due to the age of the system being 10 years old. The customer will look over the estimates and will get back to us when she decides what to do.
Found emergency drain pan full upon arrival. Removed water from pan , cleared drain. Filled primary pan with about 10 gallons of water continuously to ensure proper drainage. Also checked refrigerant levels and air filter. Attached picture of current operating pressures.
Completed annual maintenance on three mini split it indoor units and one condenser, brushed and cleaned all air filters and explained to customer how to clean them, cleaned indoor coils, inspected function and cleanliness of blower wheels which were good, delta t readings averaged 19 degrees, customer stated unit in living room occasionally makes a tiking noise, cycled system a. Few times and let run didnâ€™t hear any noises customer will call us if noise gets worse or happens more frequently, at condenser checked standing pressures which were normal, cleaned outdoor coil and around unit, cleared condensate lines. System operational and working.
Water leak caused by clogged drain line for main drain pan for evaporator coil, cleared, tested, system operational. Also added air filter (20x24x1)
Service for low water pressure: arrived to home to find pump kicking on at 40 and shutting off at 60 psi. Found that customers filter was clogged. Gave customer estimate to replace it but customer can do it on his own. Also gave customer estimate to upgrade to constant pressure system. Customer is satisfied with service all working properly at this time.
Completed annual ac tune up of one ac system. Replaced one merv 11 filter.
Performed annual AC tuneup. Tested unit. System operational.