Noah did everything I would expect from an excellent service person.
Danny was very proffesional did a fantastic job
Response from Folkes Home Services:
We love five star reviews, thank you!
Found the secondary pan filled with water. The condensate drain was clogged. Cleared the drain and removed the water. Went over a way for the customer to get a filter on the system. Tapped a filter on the back of the unit until the customer makes a filter rack for it. Recommended to change every month since there is work being done in the hanger.
Completed annual clean and service of one gas fired high efficiency boiler. Found trap overflowing and plugged with setiment. Cleaned trap and tested. No further issues to report at this time,
No AC due to tripped breaker, reset, tested, system operational, system has no filter, recommend coil cleaned.
Arrived at customers home. Completed the one dryer vent cleaning was clogged up very badly. Then looked at the other dryer vent for his other apartment on same building and recommended to do that one as well. Completed both dryer vents and hooked them both back up to dryer once I was finished.
Estimate to fix dryer vent that broke off going to the outside. May need to replace the elbow. Would also like us to check for "critters". Customer wants a dryer vent cleaning two out of the three are clogged gave estimate for dryer vent cleaning. Red to schedule dryer vent cleaning.
Performed gas cleaning, checked all components. No issues to report.
No AC due to bad capacitor at condenser, replaced, also found incorrect voltage being sent over to condenser, customer needs to call electrician to get breaker replaced in order for system to be operational.
Did gas check on high efficiency boiler all is good at this time
Install one Aprilaire 130 pints per day whole house dehumidifier, the dehumidifier will be installed in the garage with supply and return ductwork and grills, this unit is sized to handle the whole house pass through in closet/ducted in living room/music room, the ductwork will be installed in the garage and outlet in the living room/kitchen area