For this commercial facility in Lauderhill, we arrived to perform the much needed AC maintenance. We changed the air filters, belts and checked each and every system for proper operation, faulty parts and fluid levels.
During this commercial maintenance visit in Lauderhill, we performed maintenance on all the systems onsite. Most of the equipment was in great shape due to normal upkeep, but one system is in bad shape. Instead of costly repairs we recommended replacement for this system due to age and repairs needed.
Preventive maintenance complete with unit checked for proper operation