For this commercial customer in needed of AC repair in North Miami , one of their Mitsubishi ductless mini splits was not not turning on. After a full inspection of the system, our technician discovered that the display was faulty, after turning it on manually the system is back to cooling properly
We arrived to this commercial facility in North Miami to complete some much needed AC repair discovered during our preventative maintenance service.
For this commercial customer in North Miami, we received a custom part that is essential for this AC repair. We completed the AC repair and got this system up and running.
We arrived at this commercial facility in North Miami to a system that is leaking water. After a full diagnostic to determine what type of ac repair is needed our technician discovered that the drain line was cracked and the drain pan was out of place. After both were tended to, the ac system is working and cooling properly.
We arrived to complete the maintenance on commercial customer's system in North Miami. We cleared the drain lines, changed the filters and checked all key components including electrical and safety.
For this commercial customer, we arrived to perform our routine maintenance that was tailored to this customer's needs. Regular maintenance ensures peak efficiency, significant reduce breakdown and extend the life of your equipment.
We arrived at this commercial customer’s showroom for an ac not cooling and in need of ac repair. After a full diagnostic on the system, we found that the condenser coil was leaking and the system needed refrigerant. After replacement of the coils and flow switch, the system is cooling properly.
During this commercial maintenance, we arrived to service all of their systems including changing filters, belts and checking all key components for proper function. We also cleared the drain lines and pans. For commercial maintenance, we have our Service Manage goes out to create a custom maintenance plan for their systems needs.
At this commercial facility, their system was leaking water. After a full evaluation, we discovered that the float switch, used to prevent an overflow of water in the pan, and the condensation pan were both faulty and needed replacement. When the water level in the pan starts to overflow the float switch is activated and shuts the system off.
Service Johnsons control Air Conditioning split system unit, AKA Metasys display unit.
Service Johnson control 10 ton split unit and control system
Replacing a fuse