John is very conscientious about doing his job effectively and making sure I understand all aspects of what he was doing.....no surprises. He did a good job.
Whenever we have a problem, you guys are fair to take of it when it is something your techs did or did not do. We appreciate that much.
Performed Gold ESA Summer Maintenance on upstairs and downstairs Geotherm units. I checked coils, filters, amp draws on motors and compressors. Checked capacitors, thermostats. Checked 410A pressures. Units are operating properly at this time.
Performed ESA platinum maintenance on split system heat pump. I found the condenser fan motor pulling .53 amps and it is only rated for .5 amps. The motor needs replaced.
Performed ESA platinum maintenance on Gas Pack. Unit is operating properly at this time.
Performed check on Trane gas pack and found a bad control board and a cracked heat exchanger. Also the burners are rusted and not working correctly. We could not keep the unit running long enough to look for further component problems. Customer would prefer to receive a copy of report and invoice by physical mail.
Checked gas logs pilot. I found the chimney damper was open and these are unvented logs. I checked the operation after closing chimney damper and cleaning of the burner. Unit is operating properly at this time.
Quote for generator
Diagnosed unit only had two of the three burners running. Cleaned burner assembly, flame sensor, and igniter. Unit is operating properly at this time.
Completed installation of new unit and mini split and gas logs.
Wired up thermostat, air handler and condenser. Checkedpressures and operation in heat and cool. Unit is operating properly at this time.
Wired unit up temporary to give customer hear. LP furnace is running
Invoice for New Gas Logs and Mini Split in Main House
Invoice for new unit to be installed in Main House
Arrived for no cool/heat. Found unit out of R22. Also compressor keeps running so pressure switches are bad and compressor is drawing high amps and is on its way out. Recommend replacing unit.