28AUG2022 Jason B Arrived for no cool. Spoke with Jim about the issue. We were out to fix a condensate leak, sometime after that it stopped cooling. inspected pack unit, call for coil, but no compressor or fans running. Inspected compressors found high limit switch tripped. Reset system everything cycled. Before I could look at anything else it began to ran. We will have to schedule another appointment to finish diagnostic. 31AUG2022 Jason B Arrived for follow up on no cool. Found condenser fan motor on right side spinning backwards and overheating. Upon further inspection found run capacitor out. Replaced capacitor and cycled system. Head pressure dropped back to normal and system is now cooling properly.