Arrived on site and spoke to Mr. Alex Sage regarding the lack of chilling in their IT room. I gathered necessary measurements and pictures. Equipment replacement form has been submitted. Customer stated he may have the line voltage ran out to a disconnect in vicinity of likely condenser location, but was unsure at time of inspection.
Conducted PM equipment site survey.
Upon arrival the mop sink in the back room wouldnâ€™t drain. I cabled the mop sink with my 100 machine and got about 10 feet in when the water started to drain. After cabling I ran the faucet in the mop sink for several minutes and all the water drained out. Everything tested good.
Found th inducer motor to have a short in the motor windings. I replace the inducer and capacitor, the unit is way if as designed at this time.
Pulled and reset all 3 toilets in front restroom , installed new wax rings and closet bolts . Middle toilet has had a flange repair done before , if middle toilet fails , we will need to perform further work , this may entail jackhammering floor out and replacing flange . All working good at this time and no leaks .
Menâ€™s room urinal in Warehouse leaking from seal , pulled Sloan valve and urinal , replaced urinal seal , reset urinal, repaired Sloan valve , and tested all ok Cabled floor drain in same menâ€™s room , tested all ok
Cabled warehouse menâ€™s room urinals from cleanout next to abandoned toilet and from cleanout to right of urinals. Lines are draining good now , but middle right urinal still bounces water when others are flushed , i suspect itâ€™s becasue itâ€™s flood rim is lower and line isnâ€™t pitched properly .
This estimate is to rebuild 7 -1â€ sloan stop valves , and install refresh kit in each valve . This will not include replacement of any chrome valve parts . Performed original estimate as quoted , had extra parts that were required to complet repairs to Sloan valves ,tested functions of all Sloan valves , all ok . Mopped floor of water , asked customer to wait a few days for water under toilets to dry up , if water doesnâ€™t dry , wax seals are likely leaking and toilets will require further work . This will be an additional charge .
Estimate to rebuild 6 Sloan stops and Sloan flush valves
Found Lennox split system condensor compressor running without fan. I was able to locate a ruptured capacitor and replace with one from truck stock. Unit is now on and cooling with a 20 degree split temperature. Aside for obvious age the unit appears to be working well at this time