Air conditioning was blowing warm air Pickerington heating and cooling came right out and fixed the issue in a professional manner.
Guys very friendly and respected my home. Always happy with Pickerington Heating & Cooling
As always, excellent service!
He was nice, respectful and knowledgeable. He explained what was wrong. His work was fast and efficient. Thanks Isaiah ! You’re the best
Quick response time, completed job quickly
Technician was great! Found the problem quickly and had it fixed in no time!
The service tech called 30 minutes prior to arriving which is appreciated. He was knowledgeable and explained everything he checked with our A/C unit and found no issues. Bought the package to have them come back out in fall for the furnace.
Replaced an inducer motor on a Bryant gas furnace. The furnace is now operating properly and is ready for the winter season.
Tuneup was performed on a gas furnace. The system is operating properly and efficiently, and is ready for the winter season.
Customer had an estimate for a full Carrier system by one of our talented technician.
One of our talented technicians performed a duct cleaning for the customer. Pictured is the customer's Comfortmaker Gas Furnace Unit.
One of our talented technicians completed a Real Estate Furnace and A/C or H/P Certification. Pictured is the customer's General Electric Furnace Unit.
Semi annual (FALL) Scheduled Maintenance on residential furnace. Upon arrival tech went through furnace tune up list and confirmed that system is working within manufacturers specifications
Performed complete tuneup and safety inspection on a Bryant furnace to ensure efficient operation for the winter season of 2019/2020.
The technician diagnosed a Carrier furnace that was blowing cold air. He cleaned the flame sensor, and added a heat shield between the PVC exhaust and the water heater. The technician also removed debris from the the ends of the flue pipes. The system is now operating properly.
Performed complete tuneup and safety inspection on a Comfortmaker furnace to ensure efficient operation for the winter season of 2019/2020.
Diagnostic Service Call on YORK furnace/ Tech arrived on site and Customer stated the pilot light was out. Tech Waited for furnace to start and see its operation. Found the ignitor not getting hot and the gas valve will open, Ignitor has 0ohms Tech wants to replace ignitor. Customer would like to wait on replacement
Furnace Tune Up & Safety Inspection on 2018 Carrier Brand Furnace.
Performed a tuneup on a gas furnace. The system is running properly and efficiently and is ready for the winter season.2019/2020.
Furnace Tune Up & Inspection on 2012 Lennox Furnace.