Performed a home inspection. Found all outlets and switches to work as they should. Performed panel maintenance and tightened all connections. During panel maintenance found and replaced 1 50 amp 2 pole breaker that was rusted and needed to be replaced. Found neutrals under the same lugs and corrected issue. Furnished, wired, and replaced 2 t8 bulbs and sockets in a 2 by 4 fluorescent in the downstairs office with LED bulbs.