Brent ran into some complications while installing some new faucets. He stayed until the job was done well past quitting time. He definitely busted his butt to make sure it was right.
Very good job done professionally
I just had Chris in my home and this individual will always receive a 10+ rating. He is the billboard model for your company and always a superb representative of the professional. I’ll never have another company servicing my home as long as you continue to provide the awesome service you always do! 5-Stars
Very fast response and got my clogged drain fixed. Always pleased with Stritmatter’s service department
Rocky did a great job explaining the situation and recommending a way to fix our problem.
On time - personable - efficient
These guys are great, it’s also nice to see someone come to my door who I’ve seen before, nice knowing they can be trusted!
Our plumber arrived quickly, behaved professionally, and capably worked to solve our issue. Very satisfied with our service.
We have used your service two times now, you are highly recommended and we are completely satisfied with the diagnostics, the professionalism and the suggestions!
The tech that came to fix a plumbing problem we had was extremely nice and knowledgeable. The job was fixed in a timely manner and he even went out of his way to replaced our air filters!
Replaced 6 angle stops under all sinks. Installed 3 delta lavatory faucets
Plumbing tune up
Ran gas line to outdoor grill and grittle.
Replaced cap under warranty on GOODMAN outdoor unit and system resumed normal function and is cooling efficiently
Check Goodman system
Replaced Moen shower cartridge
Tuneup on two Rheem systems and cleaned both units and found some minor issues but overall systems are working and cooling as designed.
Carrier tune up
Replace toilet supply line
Quote for new air handler
Checked system and found a dead fuel run cap. Replaced cap and tested system. System is lacking in return air and recommended adding a return to the ceiling. Scheduled work to be completed.
Clear grease trap
Checked system and found burnt wires on furnace not allowing furnace to get power. Repaired wires and tested system. Found system low on R-410a and lacking in return air. Recharged system and scheduled to add return to ceiling.