We appreciate the prompt assistance, professional service, and honest evaluation.
Everything was explained very well and service was great!
Tuneup on a 16 seer 2 stage Goodman heat pump and found the unit running well and cooling efficiently. Cleaned a few components and it is cooling like a champ. Call Strittmatter’s today to schedule your appointment.
Cleaned tub drain branch line.
Quote to install customer provided carbon filter in garage.
Pulled and reset toilet
Replace expansion tank 50 gallon gas water heater in installed new vacuum breaker at hose bib
Replaced fill valve in master toilet
Cleaned sewer line
Did tune up on two Carrier systems. All operations were normal. Recommended air scrubbers, surge protection on air handlers and heat pumps. And condensate drain protection.
Did tune up on four systems. Cleared drain lines and changed all filters. All system operations were normal.
Checked system and found bad primary circuit board. Replaced board and tested system and all operations returned to normal.
Installing whole house water softener
Disconnect kitchen sink for new countertops
Fall tuneup on 4 lennox gas systems and 1 Carrier heat pump system and found some small issues but overall systems are running well and heating as designed!
Did fall tune up on 4 systems. Recommended air scrubber and condensate drain protection.