As always, the work was done efficiently and professionally.
Andy was the technician that solved a repeated problem I had with my new units. Apparently they had not been programmed after installation. Andy taught me how to program and problem solve when necessary. Thank you, Andy, for realizing I needed additional instruction on the Menu.
The plumber was extremely competent, as well as courteous. He was also very easy to communicate with.
Toby came out today to make sure our upstairs drain was flowing freely in the laundry room (we are trying to make sure to stay on top of potential issues). He was professional and knowledgeable and didn’t attempt to up-sell us on a bunch of things we didn’t need. Plus, we got to watch the camera go down the pipe!!!
Very knowledgeable and excellent service!
Checked for water leaks
Did fall tune up on two Carrier systems. All operations normal. Recommended air scrubber, condensate drain protection and surge protection.
Replaced bulb on air scrubber by AERUS on a system that we replaced under parts and labor warranty. After replacing part unit resumed normal function and is cleaning and purifying air flow in home.
Replaced drain pan and reworked primary and added float switch to secondary. Also added surge protection and compressor start assist to outdoor unit. Call strittmatters today to schedule your appointment
Unclogged kitchen sink
Checked system and found main drain line clogged, secondary drain pan rusted, system low on R-410a, safety switch on furnace cut and wired around and condenser coil impacted with dirt. Listed all recommendations and repair options.
Installed western toilet in master fixed hall bath toilet and basket strainer in kitchen sink
Checked system and found dead fuel run cap. Replaced cap and checked system Freon pressure. Recommended UV protection, surge protection, condensate drain protection and flood stop.
Checked system and found condenser blocked with bushes. Cleared bushes and washed condenser. Checked Freon levels and all was good. Changed customer provided filter do to old ones being sucked into duct work.
Checked system and found dead fuel run cap. Replaced Warranty duel run cap and all operations returned to normal.