Respectful and kind
Staff was on time and friendly. Performed the work without incident and communicated well when they were finished.
Ron and Dennis were great as usual. Any problems they faced they overcame with professionalism. They did a great job.
Very thorough and pleasant
Annual Fire Extinguisher Inspection (5 FE?)
8/19/21 confirmed with Yoon for 8/31/21 sM 5/5 Yoon would like 12:30-1:00 PM appt. Will call back km Portable Extinguishers and Kitchen Suppression Inspection Annual Extinguisher Inspection Semiannual Kitchen System Inspection Ansul R102-S3 (2)500 links (1)360 link (4)Nozzles Deficiency: Number of Systems failed : 1 Deficiency: K-Class fire extinguisher is out of hydro date. Deficiency for Ansul R-102 3 Gallon Left Side of Hood: No space between deep fryer and range. Recommend stainless steel spacer. Deficiency: Number of Extinguishers Left at Job: 1