I have had 2 very good experiences with this company.
Completed Annual Fire Extinguisher Inspection for 2021
6/1 LM/texted/emailed reminding Paul of appt. Paul confirmed km 5/26/2021 - Paul approved the appointment for 6/2/2021 at 8:30am. Christian (Mgr) will be there. RP 5/19/21 Called Paul and Reminded him of the Appointment SM 5/14/21 confirmed with Paul for Thursday 5/20/21 sM 2/9/21 called and left VM for Paul. SM Portable Extinguishers and Kitchen Suppression Inspection Annual Fire Extinguisher Inspection (4 FE?) Semi-Annual Kitchen Hood Fire Suppression System Inspection (Ansul 9gl) Deficiency: Electric non fuel source on first Henny Penny Fryer from the right. Electric non fuel source does not shut down during system actuation. The unit is plugged in outside of hood. Looks like electric power cord has been spliced together. Deficiency: Number of Systems failed : 1 Deficiency: R-102 Regulator, Expellant Hoses and Cartridge are out of hydro date. Inoperable Deficiency: Discharge warning device did not operate during system actuation. Deficiency: Scissor link holders need to b
5/21/21 confirmed with Horatiu for Wednesday 5/26/21 He will put the alarms in to test SM Kitchen Suppression Inspection Semiannual Kitchen System Inspection Ansul R102-D6 (1)500 link (2)360 links (10)Nozzles
5/24/21 Confirmed VIA Email with James for Tuesday May 25th Notice of Non Compliance and Repair Proposal Fire Systems of Michigan recently inspected the fire extinguishers at your establishment in accordance with applicable state statutes, local fire codes and NFPA guidelines. While inspecting your extinguishers, they were determined to be "Non-Compliant" per local fire codes. The attached proposal summarizes the non-compliance issues that were found during the inspection and the costs and actions needed to correct them. Please contact me as soon as possible to review the attached proposal and schedule the repair to your fire extinguishers. I look forward to working with you to bring your extinguishers into compliance. To discuss this proposal, please contact: Rob Harrison Phone: (616) 588-0746 Email: firstname.lastname@example.org EQUIPMENT REPAIR AGREEMENT This Agreement between FIRE SYSTEMS OF MICHIGAN (Company) and you (the Customer) provides for repair services only on the equipment
5/21 Confirmed with Daena km Portable Extinguishers and Kitchen Suppression Inspection Annual Extinguisher Inspection ( 1 FEs ) Semiannual Kitchen Suppression System Inspection ( 3 Ansul 3G )
Corrected deficiencies from recent inspection