I have had 2 very good experiences with this company.
Sprinkler Warranty Call Warranty to put patch on already patched pipe
12/21/22 Dry System has a leak. DH Sprinkler Service Call Service call for leak
12/15/22 Confirmed with Danyell for 102/19/22 at 11:00amish / Sent email regarding service. DH Notice of Non-Compliance and Repair Proposal Fire Systems of Michigan recently inspected/serviced the fire sprinkler system at your establishment per NFPA Standard for Inspections, Testing, and Maintenance Requirements (2017 Edition), on November 23, 2022. While inspecting/servicing your fire sprinkler system, it was determined to be "Non-Compliant." NFPA 25 (220.127.116.11) The property owner or designated representative shall correct or repair deficiencies or impairments The attached proposal summarizes the deficiency/impairment issues that were found during the inspection/service and the costs and actions needed to correct them. Fire Systems of Michigan strongly recommends that your sprinkler system be repaired to become compliant. The fire sprinkler system as-is may not work properly due to the referenced deficiencies/impairments and may not extinguish, suppress, or control a fire. This is a saf
11/21/22 Confirmed by Danyell P. for 11/23/22 around 12:00pmish DH Sprinkler Inspection Annual Fire Sprinkler Inspection (1 Wet System) Deficiency: There is no evidence of five-year internal obstruction investigation Deficiency: There is no evidence of five year fire department connection internal check valve inspection Deficiency: There is no evidence of five year fire department connection hydrotest
11/1/22 Gary called to schedule the sprinkler asked for 11/23/22 DH 9/21/22 Spoke with Gary and he will call me right back he is at lunch DH 09/19/22MV Tried calling Gary again with no answer and his VM box is full so could not leave a message. Canceling appointment until we can get in contact with him. 09/15/22MV Emailed Gary regarding inspection date 09/20, waiting on confirmation. 09/13/22MV Called Gary, no answer Sprinkler Inspection Annual Fire Sprinkler Inspection (1 Domestic System)