8/31/23 Confirmed with Pastor Don for 9/5/23 at 11:30am / DH / Sent email regarding inspection and regarding backflow. DH Sprinkler and Backflow Inspection Annual Fire Sprinkler System Inspection (1 wet, 1 dry) Annual Back Flow System Inspection/Test (2 devices) Deficiency: The church has a national time panel that has a signaling circuit issue. This was pointed out to the church by the fire marshal. When he came out to check the system out. We also noticed the panel had the trouble on there when we arrived, there will have to be a fire alarm technician Sent to this site to correct issues with system and get them back in compliance
10/6/22 Confirmed with Bill for 10/10/22 9:30ish / Sent email regarding inspection DH Sprinkler Inspection Annual Fire Sprinkler Inspection (1 Wet System) Deficiency: There is no evidence of 5 year internal pipe obstruction investigation. Deficiency: There is no evidence of 5 year FDC check valve inspection. Deficiency: There is no evidence of FDC hydrostatic test. Deficiency: Quick response sprinkler heads are outdated.
10/15 Scheduled with Paul via email Unconfirmed km Portable Extinguishers and Kitchen Suppression Inspection Annual Fire Extinguisher Inspection (4 FE?) Semi-Annual Kitchen Hood Fire Suppression System Inspection (Ansul 9gl?) Deficiency: Number of Systems failed : 1 Deficiency: Electric (fuel source on oven and non fuel source on pressure fryers and deep fryers under main hood do not de energize upon fire system actuation. Deficiency: Firing pin and cartridge in universal control head is out of hydro date.
Perform required 12 year hydrostatic test on the kitchen fire suppression system agent tank, replace agent with new, rebuild cartridge receiver valve and repalce the actuation cartridge. All work done in accordance with NFPA 17A. Notice of Non Compliance and Repair Proposal Fire Systems of Michigan, LLC. recently inspected/serviced the kitchen suppression system at your establishment in accordance with local fire codes and NFPA guidelines. While inspecting/servicing your kitchen suppression system, it was determined to be "Non-Compliant" per local fire codes and manufacturers specifications. This proposal summarizes the non-compliance issues that were found during the inspection and the costs and actions needed to correct them. Fire Systems of Michigan, LLC. strongly recommends that your kitchen suppression system is repaired so that it will become compliant. The kitchen suppression system as-is may not work properly due to the deficiencies described below and may not properly extingui
Completed Annual Fire Extinguisher Inspection for 2021