Sean W. was quick very professional!
Friendly and had patience.
On Time, efficient, and very communicative .
Very professional and efficient
Both fellas were very efficient and job the job done. They explained what they were doing and gave an accurate timeframe
Got it done
Commercial fire ppwk Complete fire alarm conversion and then annual fire alarm inspection. Complete all required paperwork.
Install a new double check backflow inside the closet where the sprinkler system is. This will help in multiple ways. The only current shut off to the sprinkler system is a PIV in the outside lawn that is currently leaking by and prevents routine work at the riser from being able to be completed. It will also be allow the sprinkler system to have better protection from cross contamination with the city which may be mandated in the near future anyways.
Annual Fire Extinguisher Inspection (3 FE) Portable Extinguishers Inspection
Wet: FDC failed the hydrostatic testing – leaks were present during the test, meaning that the connection will not withstand high pressure and may fail during a fire. Replace FDC connections and retest the line after the repair has been performed. NFPA 25 (13.8.1)