He did a nice job and attempted to not interrupt us as we were working.
All the guys at FirePros are great - professional, efficient, and easy to get along with.
Team was very professional and completed assignment in a timely fashion.
They where here at 8am and finished at 2pm. They worked hard and where very professional.
Camp answered all my questions, was very friendly, and professional
This quote is for fire pros to provide cellular monitoring for the new fire alarm panel.
**Commercial Fire Paperwork** Annual Fire Alarm Inspection NEED LIFT to get to Duct detectors. Small skinny lift that fits in and goes up 30 feet.
Jenn from Grand Traverse Pie co called in 9spoke to Autumn) that the panel in their suite is going off for one of the empty suites- showing DACT Trouble 1. needs service to check it - got it authorized by Steve G- Jenn's contact number is 231-799-5502
Portable Extinguishers and Kitchen Suppression Inspection
Annual Fire Extinguisher Inspection (2 FE)
Deficiency for FACP PANEL: **QUOTE for FACP REPLACEMENT..FACP Is not trying to break dial tone when it needs to call monitoring. Tested both trouble and alarm and panel does not attempt to break dial tone at all. This is a faraday MPC 6000 and this board is obsolete. This is a strip mall system FACP is in back X ternal riser room. Some devices in the field have modules and some are addressable I do believe. I believe there are 27 manual pulls, several smoke detectors, and,also we are monitoring the sprinkler system.It appears to be 10 businesses in the strip mall.