I've had nothing but excellent service from you guys. I appreciate your help. Dakota, Jeff and Tanya have all been great to work with.
Jason gave us a very detailed situation on our problem and explained the best economical way to go which was greatly appreciated! Excellent service!! We have used other companies in the past that we were not happy with so very happy to work with someone so dependable! Thank You so much!
. REPLACE ALARM PANEL BATTERIES OVER 5 YEARS OLD - 12 EA 2. PROVIDE NEW 5 LB. ABC FIRE EXTINGUISHERS - 3 EA. 3. REPLACE BROKEN CABINET GLASS - 1 EA. 4. PROVIDE 6 YEAR FIRE EXTINGUISHER MAINTENANCE - 2 EA. 5. LABOR 6. SERVICE CALL
Repair of 10 FX TO THE SHOP, 10 LOANERS LEFT LOCATION'S ARE ON EXTINGUISHERS WILL NEED TO HAVE A LL24 KEY
Annual Fire Alarm Test and Inspection EXT Fire extinguisher annual maintenance
Repair of 1-FX TO SHOP FOR SERVICE 10#ABC
Alarm Device - Manual Station 2249
TROUBLESHOOT 6" WATTS BACKFLOW IN VAULT TO CORRECT LEAK
Replaced batteries in fire alarm panels which failed the load test
Backflow Inspection - 5 Devices Total, Fire Extinguisher Annual Maintenance, Backflow Annual
Backflow Priority Inspection
Fire Extinguisher Annual Maintenance, Alarm Quarterly Inspection
Annual fire Alarm Test and Inspection - Units
REPAIR AND RETEST FAILED BACKFLOW DEVICE
Sprinkler Annual, Fire extinguisher annual maintenance, Standpipe testing
Fire Extinguisher Annual Maintenance, Fire Alarm inspection