Scott did a great job!
Serviceman was welcoming and informative...let me make my own decisions and did his work quickly and efficiently. Would recommend your company to anyone needing service. Thank yoi
Scott was helpful and found the problem right away and helped hook up the new thermostat
Ameriserve was here in one hour to fix my gas furnace
Mike did a great job. My faucet was very old
The most professional plumbing service we have ever encountered.
Ameriserve is great
Scott was great, second time he’s been to our house for two different fixes. I will be calling for him and Ameriserve for any plumbing issues I need in the future.
Not happy had to spend money.
Unclog bathtub drain.
Leaking boiler, teplaceded automatic fill, expansion tank, relief valve and air vent.
Install garbage disposal
Unclog building sewer with electric snake
No heat oil furnace. Client having problems with the furnace oil burner going on and off, on and off.. found micro switch in Beckett primary control with ac ready wiring strip to be defective.
No heat gas furnace. Repair broken wire and replace blown fuse. When a wire breaks inside your furnace it rubs against another piece of metal and shorts out the system and blows the low voltage fuse. High voltage shorts blow the breaker in the breaker panel.
No heat gas furnace. Gas furnace not working, when furnace is starting you can hear water spashing around inside the furnace. To un-clog furnace you have to take apart the furnace drain system and blow out the lines with high pressure air. When the furnace drain pipes are empty the furnace will start and run normal. Check us out online at Ameriservenow.com
Install kitchen sink faucet with spray. A new faucet and drain assembly can give your kitchen a new beautiful look that all your friend will notice and like. Check us out online at Ameriservenow.com
Install new Moen kitchen sink faucet with new basket streigner and drain assembly.
No heat, bad control board on oil furnace
Unclog bathtub drain by removing large hair clog.
Install customer supplied faucet
Replace leaking T and P relief valve on water heater,.high temperature or high pressure will cause the relief valve to leak water on the floor. Once the relief valve leaks it needs to be replaced because dirt gets into the seal preventing it to reset.
Unclog building sewer with electric snake. The older the plumbing system the more like it is to have a clogged drain. Over the years waste will build up in the pipe causing a clog.
Boiler leaking in basement. Your expansion tank has a air bladder that expands and contracts when water heats up and cool down. When the expansion tank fails it fill up wit water and prevents expansion of water causing relief valve to leak on floor.