Tapped into existing 1” natural gas line and installed new gas line to stove and back deck grill
Replaced 6 compression valves with CPVC angle valves in residence in Adairsville, Ga
Installed customer furnished bathroom faucets and installed new cutoff valves and p-traps. Repaired electrical on 40 gallon electric water heater in residence in Adairsville, Ga
Furnished and installed new Rheem 47 gallon electric low boy water heater and expansion tank in residence in Adairsville, Ga
Waterline leaking underground. Made repair to water line. Checked other plumbing.
Cut out section of 3" drain line in basement ceiling where leaking and repiped. Checked other plumbing
Supply line feeding low boy electric water heater had ruptured and was spraying in crawlspace. Checked plumbing water pressure and found that pressure was at 100 PSI, couldn't find pressure regulator. Installed new 3/4 pressure regulator (PRV) and gate valve on main line.
Waterline leaking downstream from meter. Excavated ground and meter box and found fitting leaking on 3/4" gate valve in ground. Cut out section of waterline and repiped and installed new gate valve. Checked other plumbing
Furnished and installed Rheem Marathon 50 Gallon Electric water heater and expansion tank. Checked other plumbing
T&P valve constantly running in water heater. Checked water pressure at 65 PSI. Drained Rheem natural gas water heater and replaced T&P valve. Checked other plumbing
Pressure tested water system and found several leaks on plumbing system. Also found high water pressure and bad pressure regulator. Gave estimate to make repairs