We thought we were smelling gas and called this company to look into it. They were very prompt and thorough, and thankfully, there was no gas leak. We will use them in the future.
Keith Lee of Georgia Plumbing Experts knows how to treat customers and knows plumbing. He is a detailed plumber and uses all of his experience to do a quality job. I will use Keith Lee to address any future plumbing issues I have in my house.
I recently purchased a 40 year home and began having septic issues almost immediatly. I live a very busy life and needed a reputable plumbing company that I could trust. Several neighbors highly recommended Georgia Plumbing Experts. I made a phone call and Keith was out within the hour. He quickly diagnosed my plumbing problems and made the necessary repairs. He and his staff are very knowledgeable and prompt, something you dont find much of these days. I am now happy to say that my septic drain issues are a thing of the past. Thanks Georgia Plumbing Experts!!!!
Will use again
We had a bad sewer odor at my work and Keith found the problem and made the repair in a timely manner and at a reasonable price
Rebuilt American Standard toilet and adjusted fill valve
Replaced flange on toilet and rebuilt with new flush valve, fill valve, and flush handle. Reset toilet with new wax seal and closet bolts
Leak on floor around refrigerator. Repaired 1/4” copper ice maker line feeding ice maker
Excavated ground and tied washing machine drain into septic tank main drain line
Rebuilt Sayco tub/shower valve with new stems, seats, escutcheons and handles
Kitchen sink drain clogged with grease. Cleared blockage on drain line with Clog Dog flexshaft
Tested water pressure at 90 PSI. Furnished and installed new 3/4” PRV (pressure reducing valve) on CPVC main waterline in home. Set pressure at 60 PSI
Repaired cold stem on commercial faucet at Ross’s Diner
Kitchen sink not draining and pipes loose and leaking. Repiped tubular drains and cleaned out grease from drains
Polybutylene waterline leaking under home. Cut out section and repiped with pex.
Sump pump not working properly. Tested for operation and adjusted float switch. Furnished and installed new high water alarm and tested for proper operation
Waterline feeding home leaking at foundation where entering home. Cut out section of 3/4” copper pipe and repiped with pex through wall and sealed with hydraulic cement.
Disconnected and capped 2” natural gas line feeding old building at master meter. Found no other leaks at this time
Repaired 2 1/2” copper freeze breaks on waterline feeding front hosebibb. Also furnished and installed new 1/2” sweat ballvalve
Installed Price Pfister bathroom faucets and rebuilt 2 toilets