Jonathan did a great job. Very polite, very knowledgeable, fixed the issue right away.
. System had very weak capacitor on the system. Causing compressor to not run at full speed. Replace with Universal turbo 200 Capacitor. Cleaned outdoor coil and verified correct refrigerant levels.
Seasonal maintenance on air conditioner
Seasonal maintenance on air conditioner and EAC.
Seasonal maintenance on air conditioner. Charge was set where it needed to be.
Thermostat batteries where bad. No common wire available on thermostat to by pass battery.
. Nest thermostat. Not giving W1 call for boiler to come on customer provided temporary state. Until nest can fix the software issue. Also replaced 3Amp fuse is furnace.
. Furnace Maintenance. Changed humidifier pad. Cleaned wiped out electric air cleaner.
Drain first fill loop while adding water to release water from zone 1 and zone 2, 1st and 2nd floor boiler loops.
Seasonal maintenance on equipment
Seasonal maintenance on Furnace.
Seasonal maintenance on Daikin furnace.
Seasonal maintenance on Daikin air conditioner
Checked and adjusted blower speed taps with Water Furnace. Cleared drain line as well . Will follow up about air flow
Added r22 to system