Very hard worker, everything left neat and clean, wore booties every time he came through the house: very much appreciated!
Kevin was very knowledgeable and did a great job getting the air conditioning back running.
Prompt, efficient, service
Great in all areas
Keith was very thorough and answered all my questions.
They are always professional, explain any issues and make multiple recommendations for work that needs to be done
Jonathan did a great job. Very polite, very knowledgeable, fixed the issue right away.
Seasonal maintenance on air conditioner
Found cracked fittings on the drain line. Cut out and removed cracked fittings and made sure drain line was clear.
Replaced dual capacitor on outdoor unit.
Maintenance and filters with replacement capacitor for first floor Spring and fall maintenance filters 2x a year and humidifiers in the fall. Repair first floor air conditioner
Seasonal maintenance on air conditioners and filters.
Replaced dual capacitor on outdoor unit. Cleaned unit and checked over.
Serviced Bryant heat pump and replaced pitted contactor.
Flushed loop and geo unit.
Capacitor was bad on the fan side causing outdoor fan not to run. Once fan was running, motor was noises and bearings found to be failing. We replace just the capacitor and not the fan motor.
Seasonal maintenance on heat pump and filter. Drain line safety had shut unit down to prevent floor from being ruined. Cleared drain line. Capacitor on outdoor unit was weak and replaced.
Recharged system and added stop leak.
Capacitor failed on outdoor unit. Contactor is pitting. Replaced both and washed outdoor unit.
Seasonal maintenance on air conditioner.
Compressor scroll plates are making noise. Found leak in accumulator will be sending price.