John did a great job with install and answered all my questions. I am impressed with the pride all the technicians take in their job.
I highly recommend Peak. Always efficient and complete. Very respectful group.
Capacitor failed on outdoor unit. Contactor is pitting. Replaced both and washed outdoor unit.
Seasonal maintenance on equipment.
. Found broken blower wheel mount had broken. Allowing blower wheel to spin out of alignment. Causing damage to the blower wheel itself and the blower motor. Furnace under 5 year warranty. So part where under warranty. Billed for one hour of labor and a dispatch charge.
Seasonal maintenance on air conditioners. Cleaned 2nd floor filter, the door has a fault code.
. Original inducer motor locked up.
Air conditioner maintenance. System in good working order at this time. Pulled and cleaned blower wheel and housing. Due to dry wall dust build up within blower. Causing burning smell from electric heating elements. Constantly when running electric heat.
. Relocated disconnect causing issues with communication side of equipment.
Replace both motor mounts and pump coupler. Motor mounts put coupler in a bind causing it to break. Once pump was repaired the boiler wouldnâ€™t stay running, found the thermostat to be dropping out at random times. Recommend a new thermostat that will fit that wall.
Move switch to avoid accidentally turning furnace off during filter change.
. Dirty filter causing an Air restriction Causing. Furnace to over heat. Filter should be replaced monthly for a one inch filter.
. Broken wire on the door switch inside furnace. Replaced spade connector to repair wire.
Seasonal maintenance on Air Flo furnace
Seasonal maintenance on Lennox furnace
Seasonal maintenance on Comfortmaker furnace.