Chris Gilham was on time, courteous and knowledgeable. Great Service, Great Experience. I wish all service technicians were as good as Chris!
This was my first time dealing with 3D air. They sent me a message to let me know that the service person was "on the way". Kevin got their on time and fixed my issue quickly - he knew what he was doing. I'll use then again.
3-D Sit has always gone out of its way to meet our HVAC needs. This company will absolutely not quit until everything is working as it should. Their fees are reasonable. Their technicians are knowledgeable and the service is alway prompt. 3-D maintains three commercial and two home units for us.
Best service in the business. Courteous, responsive, affordable. Highly recommend!
Great experience. Both techs were great and explained everything and they had all parts needed on hand which is a huge plus. No runs to HD to buy parts and extend the appointment. Will use again and recommend to others.
Tech. was very knowledgeable and did a great job!! I was very pleased with the work on my heat pumps.
Better than could have expected, but they were before after a lightning strike, should not have been the surprised.
Installed a Reme halo and Aprilaire
Drye vent clean out
Performed regular maintenance on this furnace in Pelham. Also replaced the four expired smoke detectors.
In Pelham today performing a maintenance on this furnace. This customer received $20 off by mentioning our Facebook ad. Check us out.
Today we are performing a regular maintenance on this newer Carrier Heat Pump system. Because heat Pumps run year round, it is important to keep the coils nice and clean.
Starting the Fall maintenances now. Call to schedule yours.
Fall maintenance and cleaned out the dryer vent
No cooling in Pelham
Sign the customer up on our service plan and did the a/c maintenance.
No cooling call at G&S Glass in Pelham.
Giving a quote on a business in the Pelham area on a yearly service agreement
Performing a regular maintenance on this Goodman In the Pelham area today.
Cleaning some dirty coils and getting this unit cooling again.