Although we had a new service tech at our residence for our annual winter maintenance, Mr. Joseph Walters is a highly skilled HVAC tech. Great personality, been in the business for many years and is well versed in his position. We’re hoping for a lasting relationship now and going forward with utilizing his companies services. I would highly recommend A+ Heating & Cooling and Joe Walters to those interested in having work done on their HVAC equipment.
Chris was very knowledgeable and had a great attitude.
Excellent job and very friendly.
Kevin arrived early, and was very knowledgeable about our system. He took his time and we appreciated his time and service!
Kevin is a very nice guy also I’m glad i have a one heating co.
Have a design flaw in original ductwork making it difficult to regulate a two-zone system. Christopher Thompson is very knowledgeable and helpful in recommending a solution, which we are probably going to install in the spring.
Lionel is great tech.
Affordable and sweet maintenance plan
Found the fan not plug in the capacitor all systems are working at this time
We were just out for the same reason no charge
Found defrost board constantly feeding power to reversing value And we need a new zone board to.
Came by to explain to her why the system runs and heat and emergency at the same time also explain to her what to defrost mode
Found the system to be working properly when I arrived. All temps and pressures were good. Checked the heat strips to see if that was the issue when it goes through defrost and they were working properly. Clients says that his wife may have had the thermostat set wrong but at the moment the system is operating correctly
Performed routine maintenance on a 2011 Goodman heat pump split system. During inspection found all motors working properly ,capacitor is in good shape ,contactor is good,and the heat strips are operating. I did find that the compressor is running higher amps than it should ,all this is stating is that itâ€™s starting to wear. No further action is needed at this time.
Performed maintenance on system. System is working normally at this time
Bad defrost board bypass defrost for now
Performed maintenance in heating all systems work properly at this time Duel fuel system
2015 Ruud Callback. Owner stated inside temp dropped to 66 overnight. At arrival thermostat was set at 71 and indoor temp was 71. Started system. Checked pressures. Checked heat strips. Tested defrost. System is working normally.
Performed routine maintenance on 2 Ruud systems. Checked filter, checked thermostat, checked elements and blower amps, checked the evaporator coil, checked drain pan and blew out the drain line, checked/tightened electrical connections, checked capacitor, checked fan and compressor amps, checked pressures and reversing valve, cleaned condenser coil.
Replaced two wire 10 inch zone damper per Robert
Replace thermostat upstairs Honeywell pro 5000
Found bad thermostat on upstairs zone Coming back to install new thermostat
Performed routine maintenance on a Lennox unit. Checked filter, checked thermostat, checked elements and blower amps, checked the evaporator coil, checked drain pan and blew out the drain line, checked/tightened electrical connections, checked capacitor, checked fan and compressor amps, checked pressures and reversing valve, cleaned condenser coil.