he had to come back second time because he forgot to do something and after he left I cheeped the unit and it appears he left some fast connections. i took a picture of it
Chris took the time to check everything out and solved the problem we were experiencing
Everything went smoothly and professionally.
He was GREAT. VERY INFORMATIVE. VERY FRIENDLY. THANK YOU FOR SEBDING HIM
Great technician!! Goes right to work and knows what to do. Does a good job and does it in timely manor. Thanks, Kevin.
He came early and did a great job, which now allowed me the full use of the rest of the day.
when i call them it was because of the noise. when them came he told me it was a broken breaker and they gave me an electrician to call. the electrician are the same day. my problem was that the unit was working if I didn't hear the noise I would not have called. now that it is fixed everything is working.
Performed maintenance cooling Found reversing valve stuck in the middle and letting refrigerant bleed Bye System is not cooling or heating properly customers power bill has been high 2015 Goodman not under warranty
2019 Amana system maintenance
Replace zone board full warranty
Reversing valve replaced Fix leak on suction line off the compressor 13 lbs 410a
Performed maintenance in cooling 2018 ruud Outdoor fan motor not working properly shut off and on and causing the system not to heat properly and cool in warm weather
2017 Ruud system unit is operating properly no issues detected
Replace outdoor fan motor full warranty
Preformed a maintenance on a Goodman heat pump. Indoor unit: I checked amps on blower motor and heat strips, I checked Uv light, I checked the drain pans and drain lines, I checked the float switches, I checked the coils. Outdoor unit: I checked amps on the compressor and fan motor, I checked the capacitor, I checked around the board, I vacuumed the drain line.
Install 100 amp panel for Hot tub & shop
Performed routine maintenance on a 2010 carrier system and found the system not working properly due to the txv sticking. After further inspection I found that the coil is extremely rusted. A comfort advisor is scheduled to go out today
2018 Ruud system maintenance
2014 carrier system tune up
2021 Goodman system zone board needs to be replaced
Preformed a maintenance on a Lennox unit. Indoor unit: I checked amps on the blower motor, I checked the electrical wires and connections, I checked the drain pans and drain lines, I checked the float switch, I checked the Uv light, I checked the coils, I noticed a light amount of rust on the coils. Outdoor unit: I checked amps on the compressor and fan motor, I checked the capacitor and the hard start, I checked around the contactors and the board, I noticed some spider webs forming, I wiped them away, I also noticed some wear to the contactors, I looked into the unit for rubbed wires and rust, I vacuumed the drain line, I washed the unit down with water. Pan strip
2018 Ruud system maintenance Checked filter, checked thermostat, checked elements and blower amps, checked the evaporator coil, checked drain pan and blew out the drain line, checked/tightened electrical connections, checked capacitor, checked fan and compressor amps, checked pressures and reversing valve, cleaned condenser coil. Please give us a Google review!