he had to come back second time because he forgot to do something and after he left I cheeped the unit and it appears he left some fast connections. i took a picture of it
Professional, knowledgeable and affable.
Technician was friendly and provide detail on service performed
Kevin came right out on a busy Friday. Found and corrected the problem. Kevin has been to the house several times over the past 5 years and has always done a great job!
Kevin nice young man and gave us his recommendations
Lionel was the BEST
Great service from a polite technician
Technician has been in my home before, he is very knowledgeable, explanatory,and a genuine nice person.
Great service to install ceiling fan. Had a couple of issues but Scott took care of these and the fan is installed and working great.
Joshua was superb..... very thorough, knowledgeable & professional. He is definitely a valuable asset to A+ as well as to us, all the clientele.
Service was done in a timely and professional manner.
Great company, did a full inspection of issues and detailed recommendations to consider.
2020 Goodman package Checked pressures. Checked voltage and connections throughout. Checked amp draw on compressor and fan motors. Checked capacitor. Cleaned coils. Cleared drain. Replaced UV bulb. No other issues. Unit is working properly at this time. Membership is still current.
Performed routine maintenance. Sprayed and deodorized coils. Inspected,monitored and confirmed all major components and safetyâ€™s including pressure temps relations are performing properly. Customer interested in IAQ. But needs information on them.
When i arrived unit was only running in cooling. Performed troubleshooting diagnostic and found tstat bad . Return for parts under warranty . Job completed
Unit low on refrigerant and indoor coil freezing up. Performed leak test and found indoor coil leaking. Advised homeowner and she wants to proceed with replacing indoor coil. And she became a member. Estimate done and signed job completed
Performed routine maintenance on 2 Lennox systems 2019
Performed routine maintenance. Cleaned indoor coil monitored and confirmed all major components and safetyâ€™s are operating properly except run capacitor. 7.5 reading 3.7. Replaced cap Unit is running properly at this time. Job completed. H/0 needs to speak to GM please about pricing and warranties breakdown.
Performed diagnostic and found that unit was not getting power on the outside condenser 1st floor and traced it back to breaker that wasnâ€™t labeled. Reset breaker and unit is running properly now. Job completed
H/0 not available. At home nor by phone
2/2018 Ruud and 2018 daikin mini split systems maintenance. replace UVC bulbs
Performed diagnostic and found unit out on overflow switch due to drain not pitched. I Pitched the drain and unit is on running and draining properly. Unit is running properly at this Time. Job completed
2005 Carrier R22 Checked system and found it to be void of refrigerant. Due to the the age of equipment, efficiency, R22 and cost of potential repairs a replacement is recommended. Customer is getting a price from Robert.
Ruud 14 Seer 2 ton split system $7900.00
Ruud 1.5Ton 15Seer Heat Pump Split System.
2.5 ton 16 seer lennox split 10,795
Lennox/Ruud 3Ton 15Seer Heat Pump Split System.