Chris arrived, intros himself and took care of business. Gave me summary of results and was gone. Loved it
Kevin is a great tech: very knowledgeable and polite. Well request him again, for our next service.
Very good. No changes needed. Nice service
Fast response, great work and reasonable price!
Demand call on a four-year-old Goodman heat pump split system. Estimate is enclosed for repairs.
2017 Carriers 2 systems Checked pressures. Checked voltage and connections throughout units. Checked amp draw on compressors and fan motors. Cleaned coils. Checked airflow. Cleared drain lines. Units are working properly at this time. Checked in cooling and heating
He bought a Lennox pure air filtration system he put a $500 deposit down
2016 systemis in good working order, no issues were presently detected with the equipment. Thermostat came out of permanent hold and reverted back to default scheduled programming. Thermostat should be left in permanent hold all of the time.
Put main panel door back on
Waxed and cleaned unit Got leaves from inside Rust spots will not come off
Install for customer supplied smart management modules Start it up generator
service call. The system was low on refrigerant. I found and repaired a leak on the 3/8 line at the air handler. No charge the coil was just replaced.
Took a quick peek at ductwork, did not charge, no issues.
Need to replace evaporator coil. Replaced evaporator coil put system on nitrogen then on deep vacuum weight in factory charge system is working OK at this time.
Repaired mini split drain line and fixed line hide. No further issues were presently detected. Took a quick look at the ductwork next-door, everything is in good shape.
Performed routine maintenance on 2 Goodman units 2 years old Duct work needs to be sealed. Scheduled for Tuesday of next week
2016 ruud system install UV light kit, Mr. sage purchased silver cool club membership
2015 system had a clogged drain line. No further issues were presently detected with the equipment.
Service call. The downstairs system was low on refrigerant causing the evaporator to freeze up. The valve core on the evaporator coil was leaking. I tightened the valve core and added 2 lbs of 420-A. I also flushed the drain and condensation pump..