Great service in pouring rain
Noah is a wonderful representative. Kind, knowledgeable, clean cut
Excellent professionalism and prompt with updates on when they will be arriving. Also sent me a text of his picture for security. Very respectful.
Robert showed up on time and completed the work in a resonable time.
Response from A+ Heating & Cooling- Electrical:
Glad to hear you received Great services!
The condensation pump was unplugged from the 120 outlet
Preformed service call on 1988 Coleman furnace. Furnace has leak in system and homeowner would like pricing on new system
The condenser fan wasnâ€™t starting due to a bad duel capacitor. I replaced the capacitor and checked the operation and pressures.
Preformed service call on 2019 Goodman system I reconfigured thermostat and system is working properly at this time
Preformed service call on 2014 system found faulty ambient sensor we will need to order a new sensor
Replaced whip to condenser, installed romex connector, sealed condenser disconnect, installed whip to air handler, and verified proper breaker sizes and voltage. Material list in notes.
Preformed service call on 2017 ruud system found high pressure switch had tripped I reset and system is working properly at this time
Preformed service call on carrier system and found the condenser has been corroded away client would like bid on new system
I performed the seasonal maintenance. All amps,volts, and capacitors are withen specs. The operating pressures are slightly low. The system is 17 years old and not worth investing a lot of money in repairs.
Diagnostic call on a 9 year old split heat pump system. Client wanted refrigerant put in. Checked over air handler and condenser first to make sure there were no air restrictions. Added 2 lbs of r22 refrigerant. System superheat reads within manufacturing specs at this time. Found that the leak is coming off the evaporator coil. Someone had put a dye in here. There is oil on the evaporator coil and dye. Client did not want repair or replacement options at this time. Recommend a service agreement for the system. No guarantees on refrigerant. System is undersized for the home. The load calculation calls for a 30,000 btu system not 24,000 which is whatâ€™s here. Client says that it doesnâ€™t cool properly in the late afternoons in the summer. Entered all information in the system, Put sticker on unit and gave client a refrigerator magnet.
Replaced 12-15ft of 12â€ flex duct.
Train josh on attaching flex pipe, Installed flex pipe & sealed
Preformed system maintenance on 2004 tempstar system I checked wire connections, amp draws, capacitors, duct work, air filter, refridgerant levels, coils, and drains. I cleaned coils and drains system is working properly at this time
Check the dehumidifier after re-wiring and trying to get the dehumidifier to run come to find out ecobee thermostat will not run the humidification or allow you to set it when ahead and set dehumidifier to standalone at 55% humidity installed overflow switch and drain pan underneath dehumidifier unit is working OK at this time Call back no charge for service
Finished install the rest of the outside lights.