Technician was friendly and provide detail on service performed
Joshua was exceptionally polite and courteous. He completed his work professionally and thoroughly. I benefited from special pricing and would highly recommend A+ Heating and Cooling and Joshua to all.
new HVAC install 11/20. recurring calls to address improper thermostat functions. poor installation can't be inspected by Leland official and this is 13 months after the fact. very disappointing. assumed vendor from Costco would provide quality work, will rethink that. SAD!!!
Arrives at appointed time in a professional manner. Accesses the problem and proceeds to remedy the problem..
Great technician! Very personable and thorough!
Joe Walters diligently serviced my HVAC under my contract and provided me with helpful advice pertaining to the condition of my old unit with future options for repairing or replacing in the future when needed. The most comprehensive visit I have experienced. Thank you.
Technician, Mark arrive within the time period designated. He was knowledgeable, professional and polite. Within a shirt period of time he identified the problem, which required an ordered part. He ordered the part and will schedule repair as soon as part arrives.
After returning from out of state, we found our system non responsive. A+ managed to dispatch Lionel to our home that day. He was able to have us up & running temporarily and ordered the replacement part. He is knowledgeable and presented himself in a polite and professional manner.
Excellent service. Joe was great , he answered all my questions and offered advice on how to maximize prefromance.
2020 Goodman package Checked pressures. Checked voltage and connections throughout. Checked amp draw on compressor and fan motors. Checked capacitor. Cleaned coils. Cleared drain. Replaced UV bulb. No other issues. Unit is working properly at this time. Membership is still current.
Performed routine maintenance. Sprayed and deodorized coils. Inspected,monitored and confirmed all major components and safetyâ€™s including pressure temps relations are performing properly. Customer interested in IAQ. But needs information on them.
Performed routine maintenance. Cleaned indoor coil monitored and confirmed all major components and safetyâ€™s are operating properly except run capacitor. 7.5 reading 3.7. Replaced cap Unit is running properly at this time. Job completed. H/0 needs to speak to GM please about pricing and warranties breakdown.
20x30 is filter size and I showed her how to properly put it in. Job completed
2021 Lennox Warranty call. 10/10/10 Checked system and found blown fuse on zone board. Checked all low voltage and could not find any indication of what caused fuse to blow. Checked damper opening and closing. Checked all wiring. Replaced fuse with spare on zone board. Started system and let run. System ran for 30 minutes. Pressures are good. Checked amp draw. Customer is unaware if any outages have occurred recently. Unit is working at this time.
2019 Ruud Unit not working. Thermostat blank. Checked system and found blown fuse in air handler. Checked low voltage wiring and found short caused by bad contactor. Replaced contactor and fuse. No other issues found. Unit is working properly at this time.
2018 Ruud 10/10/10 warranty. Checked system and found blown 45 mfd capacitor. Replaced capacitor, started and checked system. Unit is working properly at this time.
Lennox 2.5Ton 16Seer Heat Pump Split System.
Performed a routine maintenance tuneup. Inspected, monitored and confirmed all major components and safetyâ€™s are operating properly at this Time, pressures and temps as well look normal. Job completed
Leak in reversing valve.
When i arrived ,outdoor was not working after inspecting further I found unit out on low pressure due to no refrigerant. After suggesting to homeowner for a leak test due to the amount that leaked out. Homeowner agreed and I found the reversing valve leaking and an estimate was written ,signed and return for parts completed, homeowner needs this done before Friday please or latest Friday.job completed
Connected sensor wirelessly to Lennox thermostat. Tstat is operating properly now job completed
Performed routine maintenance on carrier indoor split system. Job completed
I installed zone sensor for Lennox communicating system. Unit is working properly at this time
Preformed a maintenance on a Daiken mini split. Indoor unit: I checked the filter, I cleaned the filter, I checked the coils, I checked the cooling temperature and the heating temperature, I checked incoming voltage. Outdoor unit: I checked amps on the compressor, I checked behind the disconnect, I checked drain line and vacuumed the drain line, I cleaned the coils, I checked incoming voltage, I checked the temperature on the line set. Everything is working properly at this point in time.