Arrives at appointed time in a professional manner. Accesses the problem and proceeds to remedy the problem..
Great technician! Very personable and thorough!
Joe Walters diligently serviced my HVAC under my contract and provided me with helpful advice pertaining to the condition of my old unit with future options for repairing or replacing in the future when needed. The most comprehensive visit I have experienced. Thank you.
Technician, Mark arrive within the time period designated. He was knowledgeable, professional and polite. Within a shirt period of time he identified the problem, which required an ordered part. He ordered the part and will schedule repair as soon as part arrives.
After returning from out of state, we found our system non responsive. A+ managed to dispatch Lionel to our home that day. He was able to have us up & running temporarily and ordered the replacement part. He is knowledgeable and presented himself in a polite and professional manner.
Excellent service. Joe was great , he answered all my questions and offered advice on how to maximize prefromance.
Reprogram zone board system is working properly
2019 Lennox system maintenance Silver renewal
2019 Lennox Checked pressures. Checked voltage and connections throughout. Checked amp draw on compressor and fan motors. Checked safety switch. Cleared drain. Replaced 20x20x5 media filter. Replaced UV bulb. Cleaned coils. Checked zone operation. No issues found. Unit is working properly at this time.
Warranty call. Upstairs thermostat blank. No power at stat base and no power at zone board for upstairs tstat. Per Robert need to order a new hub and zone 2 sensor.
2018 Carrier 2018 Carrier mini split/sunroom 2018 Carrier mini split/upstairs Checked pressures. Checked voltage and connections throughout. Checked amp draw on compressors and fan motors. Checked capacitor. Checked safety switch. Checked filters. Cleaned coils. Cleared drain lines. Checked heat strips. No issues found. Units working properly at this time.
Wants to speak to speak to management asap
2021 Lennox Warranty call. Unit was not coming on. Checked system and had voltage at air handler and zone board. Unit would not come on due to control board in air handler not responding. Will have to order a new board and return.
Replace drain pan
2016 Goodman system maintenance
Performed prepaid maintenance on a 2013 Ducane heat pump split system. Checked amp drawâ€™s on all motors checked operation capacitors are good system is running OK at this time no further action is needed
2016 Ruud system maintenance
Replaced EMC condenser motor. Prepaid warranty motor.
Performed maintenance in heating Replace uv bulb
Performed prepaid maintenance on a 2006 trane heat pump split system. Overall the system is working though it has a few issues one being the corrosion on the evaporator coil is very heavy, the other is the compressor over amping . Ultimately recommending replacement of the system due to age, condition, and efficiency. See notes.
Replaced evaporator coil and cleaned dryer vent. The dryer vent cap was also replaced, provided by the customer.