Spent time with thermostat which employee is not suppose to complete
Kevin explained to me how the inside and outside units are functioning.
Joe was on time, knowledgeable, tidy and courteous! After finishing his work he explained everything about the service to me in a professional manner. He is a valuable to your business at A+ Heating!!!!!! John Shadwick
Found a loose wire on the board and on the furnace make sure all the Molex plugs were plugged in properly and checked all wiring all systems are working
Found blown low voltage fuse Replace fuse
Found loose wire tighten wire back all system working properly at this time Full warranty
Water coming from system is due to defrost and the client was just not sure if it was normal. Checking the units further I found capacitors to be weak and I replaced and added a start assist.
Found a bad Defrost Board system is heating now and defrost board is bypass for now until we can get the new defrost board
Demand call on a miss matched carrier system with the unit on the inside being a 1998 model and the unit on the outside is a 2011. Found the unit I stop the defrost control board is not operating and needs to be replaced. The unit is also running low on Freon which is r22. I have recommended that the system be replaced due to age condition and type of refrigerant. Customer has asked to speak to a comfort adviser about possible replacement. Appointment is set for 2 PM today.
Replace blower motor collect 593.67
Found that the zone board is not the right zone board and causing the outdoor unit to lock out need to replace on board under full warranty
Replace outdoor TXV. Pressurized with nitrogen and leak test. Pull Vacuum and recharge with 6 pounds of 410a
Replace zone board Charge per Robert
Performed routine maintenance on a 2017 Lennox system. Checked filter, checked thermostat, checked elements and blower amps, checked the evaporator coil, checked drain pan and blew out the drain line, checked/tightened electrical connections, checked capacitor, checked fan and compressor amps, checked pressures and reversing valve, cleaned condenser coil
Super tuneup on a 1981 or 89 central electric air handler. There is no AC in this home the only heat source is a 15 KW heat strip and a blower. Ultimately itâ€™s running fine though I have strongly recommended to the homeowner to go ahead and get a heat pump system that will run much more efficiently in the cooling and heating season. Customer will be calling office to set up an appointment for a comfort adviser when they are ready.
Check out downstairs Upstairs unit low voltage fuse was blown change fuse all systems work properly at this time
Performed routine maintenance on a Lennox system Checked filter, checked thermostat, checked elements and blower amps, checked the evaporator coil, checked drain pan and blew out the drain line, checked/tightened electrical connections, checked capacitor, checked fan and compressor amps, checked pressures and reversing valve, cleaned condenser coil
2018 Ruud system 3/4 blower motor 480v bad