Fast response, great work and reasonable price!
Very happy for work performed
Everyone was very professional & pleasant to work with.
Kevin is very knowledgeable and explains everything.
Demand call on a four-year-old Goodman heat pump split system. Estimate is enclosed for repairs.
Put main panel door back on
Service call. The downstairs system was low on refrigerant causing the evaporator to freeze up. The valve core on the evaporator coil was leaking. I tightened the valve core and added 2 lbs of 420-A. I also flushed the drain and condensation pump..
I performed the seasonal maintenance on a 2018 rusplit heat pump.
Checked panel. John is patching drywall around panel now. Will be ready for inspection by noon. See notes
They will call when they get the concrete poured were the package unit is sitting
2015 Lenox 1 system Checked pressures. Checked voltage and connections throughout. Checked amp draw. Checked capacitor. Cleaned coils. Checked airflow. Cleared drain line. Checked inducing motor on gas furnace. UV light is good, less than 1 year. Checked system in cooling and heat. Unit is working properly at this time.
whole home electrical inspection
Return to repair sheet rock and label panel
Brand new install just a few days old. Customer was concerned the unit was not working correctly. Stat was satisfied when I got there, put the temperature down a few degrees . checked pressures with my gauges ,checked airflow . system is working normally at this time ,no issues to report.
Performed routine maintenance on a Goodman package unit 2016
Routine maintenance on a 2011 rod heat pump split system and a 2014 Goodman heat pump split system. See notes customer has asked for a comfort adviser for possible replacement on the Rudd.
Performed routine maintenance on a Goodman unit 5 years old
Helped John remove old panel, install new panel in wall. Left putty knife and piece of drywall to patch around new panel.