Great job from Carl. Efficient, polite and finished up quickly.
I received a thorough inspection of our HVAC system today, including a recommendation to install a UV light source to cleanse the air when there is high humidity. The time frame was 11- 1 and he arrived at 12:20.
Recommend to those persons that want good service.
The representative was kind and competent and was able to diagnose the problem. We were given a window for service between 12 and 1o"clock but arrival was at 2:20. It was not inconvenient but a courtesy call would have been nice.
Excellent! Chris was professional, polite and friendly. Thank you.
Technician got our HVAC system ready for winter & suggested a fix for one small problem. He was courteous & professional. Would recommend both A+ and this technician.
Replace Txv 1 yr part and labor
Add outlet under house for dehumidifier
I replaced the compressor under full warranty. I recovered 6.5 lbs of 410-A , replaced the compressor, pulled a vaccum and weighed in 6.9 lbs of 410-A.
2013 Lenox Checked pressures. Checked voltage and connections throughout system. Checked amp draw. Checked capacitor. Changed customer provided filter. Cleaned coils. Cleared drain line. Unit is working properly at this time. Will return to install UV light
Routine maintenance on a 2016 Rudd heat pump split system in a 2014 Rudd heat pump split system. Both UV systems are working fine safeties are operating normally. On the 2014 air handler I did find some corrosion on the evaporator coil educated homeowner on this issue down the road. No further action is needed at this time. Customer will call in December to renew his contract.
2018 Ruud Checked pressures. Checked voltage and connections throughout system. Checked capacitor. Checked amp draw. Cleaned coils. Checked airflow. Cleared drain line. Unit is working properly at this time.
Intalled 2 UV lights in new systems.
2016 Ruud 2017 Ruud Checked pressures. Checked voltage and connections throughout units. Checked amp draw. Checked capacitors. Cleaned coils. Checked airflow. Cleared drain lines. Replaced pan strip on downstairs system. Checked airflow. Units are working properly at this time. *see notes
Routine maintenance on two 2017 train heat pump split systems
Replaced Evaporator Coil. Paid in Full
Checked electrical and mechanical. Changed wire in outdoor whip while I was there waiting on Donta
2011 systems are presently in good working order. No problems were detected with the equipment at this time. Downstairs system saw a 45% reduction in starting amps on the compressor, hard start is highly advised.
Performed routine maintenance on 2 3 year old goodman units Customer is going to mail service agreement when it is due
2011 Rheemâ€™s 2 systems Checked pressures. Checked voltage and connections throughout units. Checked amp draw. Checked capacitors. Cleaned coils. Checked airflow. Cleared drain lines. Units working properly at this time.