Joshua did an outstanding job servicing our Trane HVAC system. He was thorough and complete. He also replaced the filters, checked the dryer vent and provided a detail summary of the service and findings with photos.
Kevin was terrific; smart, friendly, knowledgeable, concise, top notch. You most certainly have found a great employee. bill irvin
Very good service took time to explain what he was doing did not take long to figure out the problem
Technician was thorough and did a great job!
The technician was right on time, and did a through cleaning and maintenance of my HVAC unit. He even changed my air filter.
Joshua was a excellent worker
Joshua was great! He took his time and found some small issues that he immediately fixed! He explained everything and was very knowledgeable!
We have been using A+ for more than 5 years for installation and preventative maintenance. We are thoroughly pleased with their techs professional demeanor and knowledge. We highly recommend A+!!!!
Performed diagnostic and found unit out on overflow switch due to drain not pitched. I Pitched the drain and unit is on running and draining properly. Unit is running properly at this Time. Job completed
Performed super tune up special. Checked pressures, check capacitors and amp draw, tested safety switch and cleared drain line. Unit is working properly at this time. Client is considering a service agreement as well as IAQ and will get back to us with decision.
Performed routine maintenance on a trane system and a Ruud system 2010 and 2020
Gave estimate for duct cleaning and dryer vent cleaning. 11 supply vents and 2 returns. Scheduled for April 12. If we have a cancellation it will we sooner.
Gave estimate for duct cleaning
When i arrived I performed an inspection due to the concern of water leaking from unit. Immediately found condensate drain line wasnâ€™t in the condensate pump and was draining on the floor/carpet. Rearranged the drain line and connected to the pump. Job completed . He said heâ€™ll speak with office.
Performed routine maintenance on 2 Goodman systems and found The pressure switch to have rubbed wires on it causing it to blow the fuse. Fixed all wiring and added new fuse and system is working properly at this time
Performed routine maintenance on a Goodman system 2016
Performed routine maintenance on a 2016 Goodman
2015 Goodman Checked pressures. Checked voltage and connections throughout. Checked amp draw on compressor and fan motors. Checked capacitor. Cleared drain. Checked filter. Checked float switch. Cleaned coils. No issues found. Unit is working properly at this time. Customer is going to discuss with son about IAQ products. Gave estimate for stick light.
Bypass damper replaced and fix the 2 zone
Found out the low-voltage fuse was blown determined that it was the outdoor contactor I was in the low-voltage fuse to blow Contactor on the outdoor unit would chatter about every 5 to 6 seconds replace outdoor contactor and all systems are running 2021 Goodman
Reversing valve solenoid. Started system and checked to make sure reversing valve was engaging. Checked pressures. System is working properly at this time.
Performed routine maintenance on a Ruud system and found the panel to the media filter on the ground in front of it. Client needs a 20 x 25 x 5 media filter which we will return for. Well I had the system open I installed a pan strip with her approval and she will pay Everything together when we come back with the filter
Install 16 series merit 1 stage heat pump and variable speed air handler 9991.00 includes no charge UV stick light