Kevin nice young man and gave us his recommendations
great price for a check up found a problem with a/c pan. good time to fix before the season starts. Maintenace is importqnt.
Technician arrived on time and went through his findings with me before leaving.
Great job. Very nice and knowledgeable. Thank you
Chris is our go to guy whenever we need service. Can always count on him to resolve the issue
He did great. Nice, polite, & thoughtful young man
Had a great experience with Christopher Thompson from A+. He arrived promptly, took care of the problem, explained the solution and was on his way. Christopher was knowledgeable and cheerful. Highly recommend him & A+.
Phil Watson was prompt and very professional and thorough in performing our biannual maintenance service.
really impressed w/technician
Lionel Long was very responsive, professional, and thorough in his support of the Heating & A/C services which we needed. Would certainly recommend him.
Technician was great and thorough with the work he performed
On time, figured out the issues in to Heat & AC unit, got approval for repair and repaired the unit, now running as it should.
2005 Carrier R22 Checked system and found it to be void of refrigerant. Due to the the age of equipment, efficiency, R22 and cost of potential repairs a replacement is recommended. Customer is getting a price from Robert.
Performed routine maintenance on a 2014 Bryant system and a Ruud system. Ruud system is working properly but the Bryant system has heavy deterioration on the outdoor unit and as well as the evap coil in air handler Comfort advisor is scheduled to come out Pictures in service titan
Replace cut in box for two new switches
2018 Ruud system unit was not heating properly during inspection found fusible link shorted replaced link no further issues detected
I preformed a maintenance on a 2016 Lennox unit. Outdoor unit: I checked amps on the compressor and fan motor, I checked the capacitor, I checked the vacuumed the drain lines and the bottom of the unit, I checked around the contactors and the board, I washed the unit down with water. Indoor unit: I checked amps on the blower motor, I checked the capacitor, I checked the coils, I checked the drain pans and drain lines, I checked the electrical wires and connections, I checked the float switch, I cleaned the filter grills. The only thing I recommend is a ss2 float switch for the drain line for the indoor unit.
REVISED QUOTED EMAILED 3.30.22
2017 Ruud system maintenance removed bacterial growth inside air handler installed single bulb UV system.
2016 Ruud UP17 10/10/10 customer Outdoor Coil temperature thermistor needs to be replaced.
Thermostat wire was replaced from indoor unit to outdoor unit and the muffler is leaking too 2014 ruud System is running now need to come back and replaced muffler and filter dryer
There going with new system
I arrived at the property I checked both the outdoor units and the indoor units. I couldnâ€™t find any issues whatsoever, I checked the defrost board on the outdoor unit for low pressure trip, I listened closely for any rattling, I inspected both the indoor units to see if they would be the cause of the issue, again they were preforming properly
2017 Ruud system condenser fan motor is bad will have to be replaced or system to work properly
Checked system and found compressor to have failed. Evaporator coil is also heavily rusted. Due to cost of repairs and no warranty a replace,ent is recommended. No charge per Carmine. Gave estimate for repair. Customer is getting price on replacement system
2014 Goodman system maintenance replaced pan strip also installed and programmed customer supplied Wi-Fi thermostat. Please give us a Google review!
2016/2011 Goodman systems maintenance. All systems are working capacitors are showing rust and weak micro farad but still within factory specifications no action is needed at this time. replaced UV bulb upstairs, replaced both pan strips up and down systems. Please give us a Google review!