Very good job. Thanks
Polite. Professional. Knowledge. Outgoing. Prefer to have Kevin on all future maintenance checks please
Very professional and he explained what the problem was with my system and he fixed it. Thank you. Miriam Marks
Robert was very professional
On time. Tech knew what he was doing
Very good service
Installed 2 motion flood lights and 2 WP boxes homeowner supplied.
Maintenance 2x 2011 heat pumps
Fixed switch and replaced WP GFI
Owner got wrong board. She will call us when ready
Routine maintenance on a 2010 train heat pump split
1 system. 2019 Rheem Checked pressures. Checked voltage and electrical connections throughout unit. Checked capacitor. Checked amp draw on condensing motor, compressor and blower motor. Cleaned condensing and evap coils. Checked air flow throughout. Checked drain line. Unit is working properly at this time.
Replaced evaporator coil. And put in 7 pounds of 410 A into the system and system is working fine at this time
Replaced whips and breaker.
Performed routine maintenance
Replace defrost board on the upstairs outdoor unit. Replaced defrost board and system is working fine at this time
Replace blower circuit board
Performed maintenance tuneup on 2016 Lennox unit. Found drain clogged. Cleaned out drain line. Checked all connections and readings. System is operating properly at this time. Insulation in air handler is saturated. Advised client keep monitoring the unit.
2015 2 system Lennox upstairs blower motor is bad
Upstairs unit completely frozen 2016 Lennox system SSP (off for 3 hr) thaw out
Checked pressures. Checked voltage and electrical connections throughout air handlers. Checked amp draw on blower motors. Checked air flow throughout home. Checked filters. Units are working properly at this time.