Terrific very satisfied
Excellent in every way! A-plus
First, let me commend you for sending a heads-up (literally) before his arrival. It was nice knowing who was coming. Thank you. He was what one would expect to see answering my call. I could Ed have asked or expected him to do more, yet he did-service above and beyond the call of duty. Send him anytime. Thank you Sir Lionel.
I continue to be pleased with the service I get from A+ Heating and Cooling. Kevin has serviced the 4 units in my beach house for several years and I now ask for him by name. Since my duplex is a rental I am proactive in trying to keep everything in good shape so as not to inconvenience renters and Kevin helps me to that!
A+ has serviced our two systems for a number of years. Great maintenance . We have required emergency service twice on weekends and they responded quickly. Prices are reasonable and the techs are great.
Performed routine maintenance on 2 Ruud units. Replaced upstairs defrost control board per Chris T. Also installed 2 uv lights because I had found bacterial growth in both air handlers. Units are working properly at this time.
Found the defrost board stuck in defrost Rewired defrost board to get it out of defrost mood Maintenance person is here and is going to replace defrost board
3/8 filter dryer
Performed routine maintenance on a Ruud system 2014 found both compressor amps as well as outdoor fan amps to be rather high. Added a start assist to the unit. Also discussed a UV light to the home owner due to bacterial growth in air handler. System is working properly at this time
2020 Ruud system maintenance
2015 Ruud Checked pressures. Checked voltage and connections throughout. Checked amp draw on compressor and fan motors. Checked capacitor. Cleared drain line. Checked filter. UV bulb is still good, customer unplugs when they are not going to be here. Checked in heat and cooling. Unit is working at this time.
Added a piece of metal striping to keep the filter from being suck in to the unit.
Water had been leaking through return grill. Secondary pan is rusted and in need of replacement. There is no secondary pipe going down into secondary pan or a SS2 float switch in case of primary drain blockage. The secondary pan although rusted out is currently dry with no moisture. Drain line became clogged over the summer and water backed up into unit and made its way through return. Refrigerant pressures are currently good. Cleared drain line. System is working at this time however there are other issues. Condensing unit is rusting through the bottom. Corrosion on coil and rust on compressor and filter drier. Evaporator coil is also rusted. Recommend and put in estimate for secondary pan replacement and install a SS2 float switch.
2012 Bryantâ€™s 2 systems Checked pressures. Checked voltage and connections throughout. Checked amp draw on compressor and fan motors. Checked capacitors. Changed customer provided filters. Checked safety switch. Cleared drain lines. UV bulbs are still good. Checked systems in cooling and heat. Unitâ€™s are working at this time. Systems are showing signs of rust and corrosion.
Performed routine maintenance on 2 Ruud units 2017 and 2020. Checked filter, checked thermostat, checked elements and blower amps, checked the evaporator coil, checked drain pan and blew out the drain line, checked/tightened electrical connections, checked capacitor, checked fan and compressor amps, checked pressures and reversing valve, cleaned condenser coil. Unit is operating properly at this time
2015 Lennox system Unit is void of refrigerant conducted electronic leak search found evaporator coil to be leaking. Coil will have to be replaced for system to work properly
Found bad dual run capacitor replace 30/5 all systems running properly at this time
Reconfigured thermostat Wi-Fi
Diagnosed failure of ECM Blower Motor.
2017 Ruud 2018 Ruud Checked pressures. Checked voltage and connections throughout. Checked amp draw on capacitors. Checked safety switches. Cleared drain lines. Checked filters. The water at house was shut off, was not able to clean coils. Recommend UV lights installed to prevent microbial growth. Emailed estimate for lights. Units are working at this time.