Prompt, polite, professional, knowledgeable, and helpful.
Pleasant, heipful and efficient
Doing a Great Job well please
Kevin was very professional reviewed in detail all he did answered all my questions
I’ve owned the house for two years, and this was your second routine check-up. Systems have works without issues since we moved in. Two days after the routine check-up I have water coming flowing out of the pan and soaking the carpet in nearby areas. Called you back and technician said he most likely caused the issue from his drainage tube attempt to “blow down” ??? The tech arrived promptly for the second visit and cleared the tube, and changed the micro/float switch which apparently had not been working. Thrilled with the speedy service, yet a bit concerned this all happened from a routine check.....
Continue to be pleased with the services provided & the personnel dispatched to maintain our HVAC systems.
Replace outdoor coil and TXV
Pull and clean evap coil
Found that the outdoor coil is not rejecting the heat out of the refrigerant due to the condition of Coil. Check indoor coil to see if it needs to be clean and coil is clean 2012 ruud heat pump
Demand call on a 2014 carrier heat pump split system with two zones. Found the air handler and the secondary pan underneath the air handler in very bad shape due to water damage. Also found the main zone opening and closing on its own, intermittently. Customers asked to speak to a comfort adviser about replacement. Both zone dampers and the zone controller need to be replaced when doing the install . This has to be written into the sale . The bypass damper also needs to be looked at it looks like it needs to be enlarged .
Performed routine maintenance on two Goodman units
Found the dual run capacitor 35/7.5 was shorted replace the outdoor dual run capacitor 35/7.5. All so noticed that the outdoor cool heâ€™s not rejecting the heat out of the refrigerant like it should causing the unit to run at a higher pressure 2011 trane heat pump
Found upstairs system low on R22 and leaking in the evap coil on the indoor unit Customer is replacing equipment due to age and condition of a Quitman 2005 Goodman heat pump upstairs system Downstairs system 2013 Goodman heat pump
Performed routine maintenance on a 2013 Goodman
Humidity level in the house was 72% on the thermostat re-insulating the TXV bulb and clean the condensation line out to make sure that the line was clear and draining properly check charging system charge is good on system is humidity level in the house when I left at 63% and dropping Down stairs system
After a thorough investigation the heat strips were discovered to be running due to a shorted wire. The bad wire was located and substituted, no further issues were presently detected with the equipment.
Found blower motor bad replace blower motor all systems are working properly at this time
Found outdoor unit not running found breaker trip due to the capacitor being weak replace capacitor reset breaker and all systems are working properly at this time
Checked all electrical numbers and Freon pressure cleared drain line system is operating properly at this time
Ran 20â€™ whip to package unit
Performed routine maintenance on a Bryant system