They were great! They installed a new Trane AC for me that I needed, and it runs great! They installed it the next day. Also, another AC man that I knew looked at AC Pros work, after they finished, and he said they did a very good job - that they did everything right. Also, The service was wonderful, they communicated with me, and let me know what they were doing. Also, the financing options were wonderful! Joel and Paul and The Team -Zak and Adrian are great!!!
Jeff was prompt in calling and coming. No wasted time or effort. Curious to check on all performance items and then report all findings. A routine seasonal maintenance check performed well. He paused to take performance and air filter questions. Very knowledgeable. Trusted too Nicely done. Thank you
I will always ask for Joel Sisk!
Jeff quickly solved my problem
On time and efficient
I asked for the unit to be checked to figure out why condensation was happening and why it was so humid. I was told the coolant was good and there was nothing else they could do.
Technician was through and did a great job checking out our AC unit
Heating performance tuneup times one system. Changed out filter client supplied. Inspect blower, evaporator and ductwork. Tested all safety features higher limits and roll outs. Clean flame sensor, Induce her port and ribbon burners. Check thermostat for proper operations. No carbon monoxide or gas leaks detected. Hit exchanger still look like new no cracks. System operating at manufacture specs at this time.
Heat performance tuneup times one system. Client had already changed his filter. Inspect blower, evaporator and ductwork. Checked all safety features hard limits and rollouts. Check heat exchangers for cracks, found none. Clean flame sensor, and do support and ribbon burners. No carbon monoxide or gas leaks detected. Test thermostat for proper operations. System heating at manufacture specs at this time.
Completed diagnostic! Primary drain line is clogged up at sink area for upstairs system, tripping float safety switch. Homeowner will call plumber out to clear sink. From evaporator coil to sink is open.5oooo
Heating maintenance times one system. Change out filter client supplied. Check all safety features high limits and roll outs. Inspect blower, evaporator and ductwork. No gas leaks or carbon monoxide detector then home. Checked heat exchanger for cracks found none. Test thermostat for proper operations. System operating at manufacture specs at this time.
Perform 1 system heat maintenance checked safety components temperature rise checked coil and checked co levels system is heating properly at this moment
Perform new system walk thru check charge turn down blower speed at customer request tested cool and heat pump mode. We need to come back to change main house breaker from a 40 amp to 60 amp also condenser breaker on disconnect needs to be changed to a 30 amp i didnâ€™t have one in my van. Surge needs to be added after breaker has been changed and test heat strips
Heat maintenance, everything is properly, no problems found. Celeste forgot to clock out. Got side tracked. Out at 4:30.
Completed maintenance for 3 systems, all filters needs to be Changed they are really dirty. Upstairs electric heaters are working good. Downstairs/ Masterbedroom flame patterns,flame sensors, no gas or carbon monoxide leaks detected. Recommend installing Reme Halo to upstairs Masterbedroom system for $995.00 installed. Also homeowner will renew membership in spring time we just need to call her.
System was drout out found system low on refrigerant r22 found leak in evaporator coil system is fan coil had Russ come out and give options
Second opinion on install, Paul will give quote on redesign of ductwork.
Arrived to find system frozen turn system off we have to let system drout out and come back tomorrow
Heat performance tuneup times one system. Filter is still good at this time. Clean flame sensor and inducer port. Inspect blower, evaporator. Check all safety features high limits and roll outs. Test thermostat for proper operations. Mark told me about a noise he heard on the outdoor unit. I ran it in various stages to try to replicate the noise but I never could. Advise Mark to try to record it
Perform system maintenance checked heat strips amp draws changed customer supplied filter on downstairs unit tighten connections and tested temperature rise made sure drains were clear customer stated new unit wasnâ€™t heating as old was found air leakage on plenum sealed it made sure both heat strips are working both systems heating properly at this moment
Heating performance tuneup times one system. Cleaned flame sensor and into support. Blew out burner and ribbons. Inspect blower, evaporator and ductwork. Ductwork needs to be cleaned. Check for carbon monoxide found none. No gas leaks detected in home. Checked thermostat for proper operations. System operating at manufacture specs at this time.
Heat maintenance one system, cecked for gas and carbon monoxide leaks gas pressure, temperature rise and inducer draft motor was functioning properly. Recommended surge protectors.