Just takes care of business with kindness.
Tech was only here for 20 to 25 minutes and half of that was discussing my cold spots in my house. Not sure how well he checked out my heating unit in the 10 minutes he was in the attic. Usually, tech takes longer than that when maintaining my unit. Don't think I got my money's worth on this visit.
Joel Sisk was very thorough in checking my unit again; yearly service maintenance. Additionally He was here in the spring. Lastly, I had a concern with my Reme-Halo device and he was able remedy/resolve previous concern.
He knows our system and has been taking care of it for years.
Justin did a thorough job checking out my heating system and gave me a detailed rundown of what he did. I enjoyed talking with him and appreciate the care he took.
Great service . Very knowleable
AC Pros did a great job helping me with both a cooling problem and heat check! Fast, efficient, very nice and knowledgeable Associate for a great price. Way to go AC Pros!
Justin was very efficient and quickly diagnosed the problem. He then checked to make sure everything worked.
Justin came out promptly at 0800 and performed our heating units preventive maintenance. As usual quality service from scheduling through completion. Cannot say enough good things about AC Pros. Thank you Justin.
Post install walk-through on recently installed equipment. Installers will need to come back to make some corrections. Checked charge and adjusted to 10° sub cool. Installers are scheduled to be here tomorrow between 7 and 730.
Heat performance tuneup times three systems. Inspect blowers, evaporators and ductwork. Checked all safety features are limited rollouts. Test all safety features high limits and roll out. Only major issue that I found today was the main downstairs unit is producing 2 to 3 ppm and second stage heat. Advised Joe that it is the beginning of the end for the downstairs and two anticipate buying new equipment in 2023
Upon arrival checking with customer the following are my findings Heating is working to manufacture a specification found 0 parts per million for carbon dioxide And no natural gas leaking only recommendation is duck cleaning to increase longevity of the system please see pictures attached customer is going to get back to us with her decision,
Filter was loose inside the filter grill bracket. Changed out filter and make sure it would not make any more noise
Upon arrival checking with customer the following are my findings Found both upstairs and downstairs heating properly at this time only recommendations are duck cleaning please see pictures and estimates attacks informed the customer about her options she will get back to us with her decision moving forward
Same issue as before E6 on the circuit board. Spoke with Jason moat and he is scheduling him and a train commercial technician are going to come and investigate. System is jumper so that they have to turn off the breaker inside when they get too cold.
Heat performance tuneup times one system. Client changes his own filter. No gas leaks or carbon monoxide detected. System is heating properly at this time.
Reinstall door and trim Need to return with new single light fixture for attitc
Completed fall maintenance The furnaces are showing their age informed the customer about the likelihood of future repairs he understands and will keep so in mind please see attached as well as forms
Cleaned filter , checked for co , inspected flame sensor and ignighter, made sure flu pipe was venting properly, checked for any error codes and condensation lines .
Dispatched to a no heat. Checked out systems and found no issues at this time. Advised client to call us if any other issues occur.
Replaced board and tested system in heating and cooling for enough time to verify it's working correctly.
Upon arrival checked in with customer following on my findings everything is performed to manufacture specifications only recommendation is changing the filter and renewing the maintenance membership customer is going to change the filter and customer is going to wait on renewing the maintenance agreement until the next time we come out please see estimate attached
Upon arrival checked in with customer the following on my findings The system is working properly at this time system has zero ppm for carbon dioxide and no natural gas leaking at this time all electric measurements are within manufacturer specifications only recommendation is UV light to increase longevity of the system please see estimates attached
Changed filters , checked for co , inspected flame sensor and ignighter, made sure flu pipe was venting properly, checked for any error codes and condensation lines . Installed weather guard