Joel the technician has been servicing my house for years, a very knowledgeable and easy guy to talk to. Explains what he is doing and gives recommendations when necessary. Does not oversell products.
Excellent thorough system inspection -!! Good work !
Joel has serviced our AC units for many years. He is very good at his job and is very nice.
Jeff Stevens always does a professional job.
John was very professional, friendly and helpful during my scheduled maintenance.
Jeff came out to handle the seasonal maintenance on our A/C unit. He is thorough, competent, friendly, and ready to answer any questions!
Efficient but thorough and very professional and polite.
AC performance tuneup times one system. Changed out filter that client supplied. Cleaned off blower that had a growth on it from the age of the system. Cleared primary drain. Checked thermostat for proper operations. Check outdoor unit. Refrigerant level is good at this time. Given the age of the system which is 12 years old it is getting close to its life Expectancy in Texas wash condenser coil.
Performed ac maintenace. All pressures, amp draws, and pressures are good. System is in great shape for its age.
Call back from earlier. Arrived to find evaporator coil slightly frozen over checked charge and added 3 pounds of R 410A
I'm surprised this 2002 still running like its new, bad components changed out Contactor indoor blower is bad needs new one asap
Completed maintenance inspection, washed condenser coils, flushed drains lines, replaced media filter provided by homeowner. Blower/ condenser fan motor is range. Compressor start up amperage was a little hi. System is 18 years old and on borrowed time, life expectancy is 12 to 15years.
Call back no cool upstairs. I verified the upstairs unit is low on our 22. Advise Diane not to purchase any this year because it is too expensive. Kevin is on his way to give him some options to change out the upstairs unit. No charge today
Performed spring check on upstairs/downstairs systems, both units are working fine. Masterbedroom system is low on refrigerant, performed electronic leak search Evaporator is leaking. 4 ton horizontal box evaporator coil.
Call back from yesterday. Found drain line clogged at the evaporator. Cut the line and remove the clog physically. Then I flushed the line with hot water. The quick blast and cleared with nitrogen. Also fixed air leak at evaporator coil.
Completed diagnostic, found East system low on refrigerant, replaced shrader at suction line, which was stuck open leaking refrigerant. Added 3pds 410a and performed electronic leak search. Left sub cooling of 12.5 and replaced 20x20x4 media filter, which it was not in the system. This is a bill too job.
Preform HVAC maintenance on indoor also outdoor unit, system operating very good , put drain solution also washed outdoor coil
AC performance tuneup times four systems. Changed out filters client supplied. Inspect blowers, evaporators and ductwork. Verified and cleared primary drains to show they are flowing properly. Check thermostats for proper operations. Check outdoor units. All refrigerant levels are at manufacture specs at this time. Washed all condenser coil. Systems are operating at manufacture specs at this time.
Found upstairs system low on refrigerant, performed electronic leak search. Evaporator coil is leaking and recommended replacement.
HVAC preventive maintenance check unit operation homeowner need pricing on a 28 1/2x 14 1/2 filter rack for attic area upstairs unit and for the mrs office space area supply grill is a6 inch supply, he needs a 10 to 8 reducer with damper also 10" supply grill with flex , problem solved !
Perform a 3 system maintence drains are all clear , treated the drains checked the ductwork and changed the filter on all 3 systems. Also washed up all 3 condensers Masters system has a 5 degree. Also checked Freon levels and run capacitors, everything is working great. Also replaced all three media filters.
Preform HVAC maintenance checked indoor and outdoor unit, checked drain also motor amps are in range . Washed aslo check outside condenser subcool 11.5 that's good