On time as scheduled. Very efficient.
AC pros did a great job making sure our new HVAC system was the right one for us, amd that it was installed and working correctly. Complete professionals and vey customer centric.
Joe was very professional. He explained clearly what he was doing, thoroughly checked everything, and was polite.
Once again, Joel Sisk does a great job taking care of our HVAC system.
Jeff gave notice of his visit, arrived promptly and performed a quick but thorough check of my somewhat new unit, both outside and inside. No issues found, he noted that my filter should be changed in about two months.
Joel goes the extra mile to help a customer with a service problem. No matter what it takes, when he leaves your home, you know you have received top-notch service. Thanks, Joel, for a job well done.
Francisco called ahead of time to let me know he was on his way. Showed up very professional w/ slip on shoe protectors inside. Performed the maintenance and went over the report with me. Very good service.
Very efficient and On time Outstanding
Perform 1 system maintenance checked pressures split tested capacitor, washed condenser coil put noise isolator to stabilize pad it was wobbling specs are on maintenance form system is cooling properly at this moment
Perform 2 system maintenance checked pressures split washed both condenser coils also changed customer supplied filters specs are on maintenance form both systems cooling properly
Completed maintenance check, drains lines are clear, filter is clean, refrigerant levels are in range. Everything seems to be working properly.
Perform 1 system maintenance checked pressures split tested capacitor changed filter from van stock system is currently low on refrigerant explain customer of problem recommended comfort consult to come out and give her options. system is 19 years old r22 she said she will wait
Completed A/C check on garage system. Everything was functioning and cooling properly. Temperature split was 16.5 in range. Upstairs system 21 degree differential and downstairs 19 degree differential.
System was frozen solid, we will schedule to come back and rediagnose tomorrow. Completed diagnosis, expansion valve is bad causing low suction temperature and system to fall into freezing. We need order part and reschedule asap. 4TXCC009D3HCAA. S#20182RKBCG
AC performance tuneup times one system. Treat drain lines with drain solution. Inspect blower, evaporator and ductwork. Remi halo bulb is defective. We just installed last year. Office is ordering a new one and will call and schedule date to return to install. Check outdoor unit. Change out filter client supplied. Refrigerant level good at this time. Wash condenser coil. System operating at manufacture specs at this time.
Performed A/C maintenance inspection, filters and drains were fine. Washed condenser coils, run capacitors and start assist are in range, refrigerant levels and sub cooling are also good. No problems found.
AC performance tuneup times one system. Change out filter client supplied. Inspect blower, evaporator. Checked thermostat for proper operations. Check outdoor unit. Refrigerant level good at this time. Test capacitor and contactor. Wash condenser coil. System operating at manufacture specs at this time.
AC performance tuneup times two systems. Inspect blowers, evaporators and ductwork. Moved downstairs thermostat over 12 inches for Michelle. Test both thermostats for proper operations. Treat both drain lines with drain solutions.Check outdoor units. Refrigerant levels are good on both systems at this time. Test capacitor and contactor on downstairs system. Upstairs has the drive and has no contact her or capacitor. Wash both condenser coil â€˜s. System is operating at manufacture specs at this time.
Primary drain was clogged up, cleared drains.
Upstairs system was low on 410a, charged system with 4 pounds of 410a. Customer knows that system needs to be replaced. Had conversations with Jim the comfort advisor. No warranty or guarantee on refrigerant.
AC performance tuneup times two rooftop units. Inspect blowers, evaporators. Cleaned evaporatorâ€˜s with cleaner. Test capacitors and contactors. Wash condenser coil â€˜s. I had to remove the hell guards to clean the condenser coil â€˜s. Refrigerant levels are good at this time. Replaced filters. 4~20Ã—20Ã—2 filters and 4~20x25x2
Perform 1 system maintenance checked pressures split washed condenser coil specs are on maintenance form system is cooling properly at this moment
Completed maintenance check, Drains are clear, condenser coils were dirty, washed coils. Run capacitor/fan motor and compressor amps are in range. Recommended adding start assist to system. Everything else is good working order.