Joel Sisk came to our home on time and fixed our furnace in a very short period of time.
They were great! They installed a new Trane AC for me that I needed, and it runs great! They installed it the next day. Also, another AC man that I knew looked at AC Pros work, after they finished, and he said they did a very good job - that they did everything right. Also, The service was wonderful, they communicated with me, and let me know what they were doing. Also, the financing options were wonderful! Joel and Paul and The Team -Zak and Adrian are great!!!
Quick response. Very professional and polite. Corrected the problem in about 20 min. Addressed my concerns, and explained what he did to to correct the problem . Very pleased with his service.
I have been doing business with AC Pros for many years, and the service is always very professional and skillfully executed. I recommend them highly!
On Time and fast
these 3 men were superior in knowledge, ability and courtesy They were methodical, following the needed repair plan. Outcome has reinforced our continued desire to work with AC Pros only.Your apprentice did a really good job; we were impressed.
The technician showed up in allotted time and inspected, found issue and fixed it. Very professional and knowledgeable. The price of the item repaired was extremely high.
Excellent. Warm and friendly. Knowledgeable
Change out circuit board that I condemned last year. System is operating at manufacture specs at this time.
Install customers appliance module. The one that I brought would not reach her thermostat. Carol is getting some quotes for a new breaker panel. Since federalâ€˜s are outlawed. I will install new disconnect and whip after words. Because I do not want to turn this Federal breaker off and risk it not coming back on.
Install three 120 V window units to get client by until tomorrow when the new system will be installed
No cool. Compressor has gone to ground. Russ to give quote tonight between 6 to 7
Arrived to find water leaking on secondary outside. Secondary port was tied to outside drain. Removed and move drain to drain pan and pour drain solve to p trap system is draining properly no charge since itâ€™s on labor warranty
Perform 1 system maintenance checked safety components and cleaned flame sensor changed customer supplied filter system is working under manufacture specs at this moment
Arrived to drain lines clogged and water and slab coil drain pan rusted leaking water thru the ceeling clear drain lines removed water from drain pan and put a bucket under for the time being. We need to replace drain pan for slab coil tuff attic didnâ€™t have one in my truck will contact office to have it schedule asap
Drain pan and Float Switches
Completed diagnosis, condenser was working without a call for cooling. Contactors was sticking closed causing system to freeze up. Installed sealed 40 amp contactors and hard start kit, system is cooling at this time. Advised homeowner system is 21yrs. Old and life on system is about 15yrs. Declined replacement right now.
Perform 2 system maintenance checked pressures split changed filters also washed condenser coils specs are on maintenance form both system cooling properly at this moment
Upstairs unit that is leaking downstairs onto the master lavatory plugs needs to be illuminated. Sump pump that will deliver the water from that unit to the upstairs unit. I will be be back tomorrow to install
Arrived to no cool found burn contactor replaced all still under labor warranty so no charge system cooling properly at this moment
Performed x1 maintenance check, drains, condenser coils, refrigerant levels and customer will replace filter. Everything is in spec.
Arrived to no cool found outside unit not coming on , found lose wire rewired it checked refrigerant levels they are fine. Advised mr Wayne to sign up for maintenance program system cooling properly at this moment
AC performance tuneup times two systems. Filters good at this time. Treated drain lines with drain solution. Inspect blowers, evaporators and ductwork. Sealed up air Lakes on older system. Checked thermostats for proper operations. Checked outdoor units. Refrigerant levels are good on both systems. The older system is running extremely high amps. It is a 2.5 ton system. Pulling almost 14 amps. Newer system is running just fine. Given the age of the system which is 20 years old and the high amps it is pulling which means the electricity it is using, recommendation is to change out that system. Russ to come give a quote next week on Monday between one and 3 PM.