these 3 men were superior in knowledge, ability and courtesy They were methodical, following the needed repair plan. Outcome has reinforced our continued desire to work with AC Pros only.Your apprentice did a really good job; we were impressed.
The technician showed up in allotted time and inspected, found issue and fixed it. Very professional and knowledgeable. The price of the item repaired was extremely high.
Excellent. Warm and friendly. Knowledgeable
Had a leak after service, but it was handled promptly by AcPros. Diywall repair was also completed promptly. Was a check up visit covered by service contract.
Jeff was very pleasant , efficient and gave great customer service !
Always feel ... my HVAC... is at its optimum best... when Joel does his trade... I am buying piece of mind, for the summer...
Very professional. Customer oriented. Appeared to do a thorough inspection/maintenance of my system. I feel he did a great job
Jeff was a pleasure to deal with and very helpful Great Service as always.
replaced leaking evap coil with new trane box coil
No cool zone system. Arrive to find low pressure cut out indicator on 950 thermostat. I pulled the electrical panel off to access the IFC board high-voltage wire nut Had vibrated loose and parked against the 3H line that travels through the drive of the condenser. I soldered the copper were the electric shorted out. Charged unit 22Â° sub cool. Need to return tomorrow to top off unit.
No cool single system. Arrive to find compressor not running. Check the run capacitor 75+5 ÂµF was reading 25 on the compressor side. Removed and replace with new turbo 200 X. Part comes with a five year warranty. System cooling properly at this time. Recommend 6 in filter rack. 399.00
No cool. System was low on refrigerant. Added 3 pounds of our 410 a. System is cooling properly at this time. Need to come back and do leak search
No cool. Condenser not coming on. Found broken common wire in the outdoor unit. Made necessary repairs and sister came on and operating properly at this time.
Adjusted dampers throughout house at customers request. She's satisfied at this time.
Arrived and found leak in evaporator coil we will come the 18th to replace it
Evaporator coil is frozen, system needs to thaw out. Reschedule for tomorrow if possible please.
Hey Sue performance tuneup times one system. Filter needs to be changed, Eric is supposed to get one. Checked thermostat for proper operations. Verify primary drain is clear at this time. Check outdoor unit. Refrigerant level good at this time. Test capacitor and contactor. Wash condenser coil. System operating at manufacture specs at this time.
Perform 1 system maintence checked pressures and split specs are on maintence form replace capacitor with turbo found capacitor dead and compressor pulling high amps system is currently working on specs
Perform 1 system maintence washed condenser checked pressures split is good adjusted airflow towards rooms system is losing efficiency and amps are high so is discharge pressure system is 15 years old I recommended customer system replacement due to age and efficiency can confirm system is cooling at this moment
Found where new evaporator is leaking. Installers need to return to level evaporator. It is set to where the water flows backwards. Installers will be over after install in Richardson
Cleared out primary drain line.
A/C maintenance check out is complete, inspect drains, contractors, electrical components, refrigerant levels, run capacitor, compressor and fan motor amps. Condenser coils are clean.
replaced ductwork - performed dryer vent cleaning - will return next week to replace boots (wasn't advised on original proposal)