AC Pro’s is THE BEST AC/Heating company by far! They have one of the best technicians that I have ever known! I have had the pleasure of calling AC Pro’s for AC/Heating services for almost 20 years. They are simply the best! Joel is a great example of how to keep customers. The man is extremely knowledgeable and very precise in his work. If you want the best, call AC Pro’s!!!!!
Very professional and did the job well . Did everything as required and would like to have him do the fall maintenance as well .
Wonderful service.very professional.
Cole, from AC Pros, has serviced our AC units a couple times and I'm impressed by his professionalism and his attention to detail.
Called AC PRO’s and Cole the technician came right out, diagnosed the problem and our system was fixed as quick as that! Cole was very knowledgeable and thoroughly checked out our system. AC PRO’s are THE BEST!!!!!
Joel has serviced our unit for many years. Always a great experience. Thanks!
Jason provided great service, explaining and showing everything. It help me overcome my previous negative view on this company due the previous technician who visited my place.
Cole and AC Pros are fantastic! Coke is always so good!
AC PROs are the best! Jason came out to do the Fall service on our system. He was very professional and knowledgeable about our Trane system. If you want the best from installation to routine maintenance on your ac/heating system, call the best - AC PROs!
Perform 2 system heat maintenance checked all safety components cleaned flame sensors changed filters 2-16x25x4 need to collect for those checked co levels and temperature rise recommend duct clean and replace secondary drain pan on older system
Heating performance tuneup times one system. Change out filter client supplied. Inspect blower, evaporator and ductwork. Inspect heat exchangers for cracks. Found none. Clean flame sensor and inducer port. Test all safety features are limits and rollouts. No carbon monoxide or gas leaks detected. Check thermostat for proper operations. System operating at manufacture specs at this time.
Completed maintenance inspection, compressor is has hi cranking amps on start up ,69 rated at 90. System life expectancy is about 12 to 15 years and it's 20yrs. Old. Also drains lines/ run capacitor is good, refrigerant levels/ superheat is 18. Recommend adding start assist which is $318.95 or replacing system, Homeowner declined at this time.
AC performance tuneup times one system. Filter was recently changed. Inspect blower, evaporator. Verified primary drain is clear. Checked thermostat for proper operations. Check outdoor unit. Refrigerant level good at this time. Wash condenser coil. System operating at manufacture specs at this time.
Perform 1 system maintenance checked pressures, temperature split washed condenser coil system cooling properly at this moment
Completed maintenance A/C. Check, everything is up to manufacturers specifications.
Completed maintenance inspection: Washed condenser coils, drains are clear, installed Turbo 80 microfared capacitor and hard start kit on downstairs compressor. Fan and blowers are good, no other problems found.
Perform 2 system maintenance washed condenser coils and clean p trap changed customer supplied filter system is cooling properly at this moment
Perform 1 system maintence checked pressures and split added 1 lb to get subcool to 10 degrees system operating in manufacturers specs
Completed maintenance check, flushed drains, replaced media filter per customer. Run capacitor and refrigerant levels are good. Blower and fan motor amps are range. Compressor start amps were good.
Perform 2 system maintenance clear both drains changed filters checked pressures and split sensing bulb was not tight on downstairs system went ahead and tighten it both systems are currently working on manufacturers specs
Perform 1 system maintenance clean condenser check split and clean clean effects split and preassures good ductwork looks great recommend adding a 4 inch filter rack also clean effects works better and the dust gets catch by a 4â€ filter Other than that system is cooling at this moment.
No cool heat pump system. Upon arrival I put thermostat in to cool mode heater came on. 24 volts was not energized and the switchover valve. Found two broken wires light repairs and system came on and operating properly at this time.. She will call Monday to pay her Bill.
Cleared primary drain lines, also replaced pvc male fitting at evaporator coil on D/s system. Also quoted 249.00 on 14x44 emergency drain pan for slab Trane coil.
Perform a 1 system maintenance changed filter washed condenser and checked pressures and split system is currently running on manufacturers specs recommend insulation to Kathy shes low and it can help her system runtime and extend her new systems life.