Technician was through and did a great job checking out our AC unit
Joel always does a good job. If he didn’t, I would not ask for him every time I order a service call.
Quick getting here and fixed it fast!
Install crew arrived on time, listened to concerns, and promptly and efficiently completed work. Respect and care were shown to our home, furnishings, and accoutrements. Crew used drop cloths, removed old equipment, packing material, odd debris, and swept floors upon completion. Nice job, most professional.
Joel completed the new install walkthrough--very thorough.
The gold service plans saves money.
Francisco responded quickly and repaired our AC without issue. Signed up for the AC Pros annual service because of his excellent work.
Nice man and helpt
No cool. Batteries were dead and thermostat. Acquired two from the tenant. System came on Iâ€™ll check the charge and it was good. Kenneth is going to call the office to pay the $85
Perform 3 system heat maintenance checked safety components co levels checked heat exchangers and cleaned flame sensors also changed customer supplied filters. Found bacteria growth around some grills advised customer for duct cleaning and also further inspection of ductwork when Paul comes Monday all 3 systems heating properly
Completed inspection on two furnaces, replaced flame sensor on downstairs, not sensing enough micoamps. Customer declined surge protectors. No gas or carbon monoxide leaks detected. Informed homeowner that both units are 15 to 20 years old, it's about that time to look in to replacing them. Declined right now.
No cool. Found condenser not running. Found a burnt common wire on the contactor and capacitor. Removed and replaced with a new wire. Upon start up the compressor was running but hissing through the bypass. Which means it was overcharged. Had to reclaim around 2 pounds of R22. Compressor still has semi high amp draw. Washed condenser coil to help the fan and compressor. System is cooling properly at this time.
Performed heat inspection, flame sensor and hot surface igniter needs to be Changed out. Homeowner declined repairs at this time. Also recommended surge protectors to protect electronics from power surges. No other problems detected.
Completed heat check, performed gas and carbon monoxide test, no problems found. Recommend adding a Reme halo and ductwork needs to clean. Customer declined making any repairs right now. Everything is working properly.
Took all wiring loose and re-secured everything in the attic. Fan speed was on low for some reason. Changed it back to high. system is operating properly at this time.
Removed. Styrofoam from blower housing. Also cap primary drain line, so evaporator coil can drain properly.
ISSUE: Found water on emergency drain pan drain pan doesn't have a float switch.also water is stuck on primary drain pan due to unit not being leveled correctly will need to relevel and change out supply plenum its condensating and not sealed correctly and insulate ofc p trap REPAIR MADE: rehang trane airhandler, replace supply plen (12x20), install pan switch and insulate p-trap
Completed diagnostic! Primary drain line is clogged up at sink area for upstairs system, tripping float safety switch. Homeowner will call plumber out to clear sink. From evaporator coil to sink is open.5oooo
Perform 1 system heat maintenance checked safety components temperature rise checked coil and checked co levels system is heating properly at this moment
Perform system maintenance checked heat strips amp draws changed customer supplied filter on downstairs unit tighten connections and tested temperature rise made sure drains were clear customer stated new unit wasnâ€™t heating as old was found air leakage on plenum sealed it made sure both heat strips are working both systems heating properly at this moment
Heat maintenance on 2 ton system newer unit, everything is up to specifications, no problems. 5 ton system no display at thermostat. Repaired high voltage wires inside of furnace electrical box, which was not secured good enough. All operations are fine at this time. Also recommended adding a Reme Halo to main system for $995.00 installed, Homeowner will think about it.
Arrived to find system extremely low on refrigerant found a leak on filter drier itâ€™s under workmanship warranty will have installer come out and install new filter drier and charge system up no charge
Perform 3 system maintenance checked all safety components checked float switches operations also put tablets for drains and checked co levels advised customer to change filter for upstairs and living room area all 3 systems heating properly at this moment