Very professional; great identification of the problem and personal effort to show us how to resolve it
Jeff is very conscientious and was apologetic when he had to leave the house without being able to fix the problem the first time. He also came out to help the wiring team when one of them didnt show up.
Francisco was very helpful and worked quickly to diagnose the apparent cause of the A/C problem.
Jeff helped me out on an emergency call on a Saturday at 9:00. Super helpful. quickly diagnosed the problem, and was very efficient.
Thanks, Joel .. . for being on time for identifying the problem for explaining it to me, and and fixing it quickly!
Completed check out, don't have properly voltage going to outside condenser, customer will call electrian.
Cut to buy for her to fit into return to attempt to stop the popping one unit goes off. It seems to have work
Advised customer to call a plumber to clear drain.
Perform 1 system maintence washed codenser coil changed filter and replaced weak capacitor for turbo system cooling properly at this moment
Perform 1 system maintence found system low on refrigerant which indicate a leak in system Joseph decided to just add refrigerant for right now I added 3 lb system cooling at this moment
Completed diagnosis, need 3/4 blower motor 115 volt, also belly band with motor universal. Jeff only and quote price.
Joel has got this service call
System was low on 410a, declined leak search. Added 4 pounds of 410a. No warranty or guarantee on refrigerant.
Perform 1 system maintenance change filter washe condenser coil and adjusted airflow settings to 400cfm mr morales concern about system not satisfied and over working went in attic and it was 150 degrees will have Jim come out and use heat camera to find heat sources and we can be able to find solution
System not keeping up check charge and added 2 pounds are 22. Condenser coil needs cleaning. I advised client to do it as soon as possible. System is cooling properly at this time.
Arrived found primary clogged restrapped with pitch, clean p trap and treated the drains water is now draining recommend customer to have a plumber re rout primary because itâ€™s tied into master bedroom primary to avoid this isssues later on and we can re run the drain after plumber is done he will stay in contact with us about plumber rerouting primaary to a sink that way we can get this problem solve once and for all
AC performance tuneup times two systems. Inspect blowers, evaporators and ductwork. Verified primary drains are clear at this time. Filters are good at this time. Both systems have good temperature drop across the coil â€˜s. Checked outdoor units. Test thermostats for proper operations. Refrigerant levels good on both systems. System is operating at manufacture specs at this time.
Mr. Pierce stated that the unit was losing temperature yesterday. Arrive today and checked the charge on the system. Charge is good. I tested capacitor â€˜s. All capacitors were within specifications. Opened up side panel to condenser coil. System was clogged with dirt. This would cause the compressor to shut off temporarily and come back on once it cools down. Once I washed it compressor is quieter system is cooling properly at this time.
Compressor was off on a thermal limit. Call down compressor and recovered 1.5 pounds of our 410 a. System came on and I adjusted the charge to a 15Â° sub cool. System is 16 years old pulling 21 A and second stage.
Completed diagnostic, system was low on refrigerant Added 4 pounds of 410a. No warranty or guarantee on refrigerant. Declined replacement of system at this time.