Just takes care of business with kindness.
Jeff was professional and gracious.
Thank you! Great service. Also polite and knows his stuff.
Excellent in every way.
Great job servicing my AC today. Thank you!
The young men were so helpful and considerate.
Jason was great! We have used AC Pro’s for years and he is the best tech ever. Would welcome back every time I we need service.
Cole did a great job. He solved the problem we were having!
Performed heat maintenance everything is working properly changed filter for $55
Filter was loose inside the filter grill bracket. Changed out filter and make sure it would not make any more noise
Wasnt flame sensor , was actually the zone board that I replaced . System now working properly.
Found flame sensor bad . Need to return with one tomorrow
Checked filters and fl as me sensors and verified inducer motors were running properly and flu pipes were connected . Checked condensation lines and performed a co test. The 2016 upflow had some gaps around plenum so I sealed it up for customer. Suggested and spoke about Remy halo benefits but not interested at the moment .
Performed heat PM on 3 units . Changed filters , checked flame sensors and ig lighters and checked for any error codes . Inspected flu pipes and the overall operation of these units in heat . None of them had float switches and the oldest one has had some condensation issues in past so I installed one float switch for now and she will get the others next time.
I was Dispatched to replace the cool and heat relays.
Universal blower motor I was Dispatched to replace a Blower Motor On a RTU. I (We , Justin and I) replaced the Blower Motor. After installing the Motor I discovered the Motor was constantly powered. I found the Heat Relay stuck closed and the Cooling Relay coil was shorted. I temporarily wired the Blower Motor to run constantly until we can bring back the correct relays. The A/C will cycle normally. We also repaired the Server Room A/C as well. The new transformer we open. A factory defect.
No cool on one of two units again. Found bad Transformer on other unit. Replaced with new and wash condenser coil. That system only controls the electrical room. It only has one duck from the rooftop unit to the electrical room. The part that controls the office has a bad blower motor. We are checking availability and price now.
No cool on two rooftop units. One unit had a defective contactor and transformer. The other unit is not sending power to the disconnect on the roof. Systems are 25 years old. Recommendations today are to get a maintenance on systems. Clients can contact us after power is restored so that we can check the 3-ton unit. 4 ton is cooling at this time. All three condenser coils are 85% impacted with dirt.
East unit was not cooling, Replaced warranty 40/5 microfared everything is functioning ok.
Maintenance X 1 everything appears to be functioning as expected. At this time. The Customer wants to renew his MA in the Fall.
Completed diagnostic, installed Turbo 70 microfared run capacitor, checked charge everything is functioning fine.
Drains were clogged up tripping safety switch. Flushed drain line. Everything is up and running.
Preform HVAC maintenance on one unit 410A system with two control thermostat, change also check system drain and filter. Homeowner supply there own indoor blower amps are .4, checked outdoor unit refrigerant level also amp draw on motor also compressor 7.5 motor amps are 1.0